Ruud Furnace won't turn on
Take of the access panel on the furnace and look for a wiring diagram either on the back of the panel or inside the housing. There will be a diagnostic chart on it that will give you a hint what 2 flashes mean. I think it is a "no Ignition" code. If it is, with the access panel off and the door switch taped in the closed position, the furnace will try to start if the thermostat is calling. You want to look at the control module to see if it is flashing, then you should notice a small fan that pushes out the combustion products start to turn. Then if you look in a small view port, you should see an orange glow followed by a clicking noise at the gas valve. Then you should notice a blue flame in the view port. This flame must stay on for 5-6 seconds or the unit will turn it self off. If one of these do not happen, you will need a technician to troubleshoot it. Check to see if all wires and hoses are tight and in place. Make sure your condensate hoses are not blocked and free of water. Make sure there is no blockage in your vent pipe(s).\015\012\015\012
Let us know what you found.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
I have a white rogers thermostat, it wont click on automatically when it is colder in the house than i have the heat set on. furnace just pops, fan does work and does blow hot air when i turn it to on. i have a digital thermostat. i reset all the programming for it, even turned it off and turned off the furnace with 2 breakers at the bottom of the furnace but still nothing. The furnace is warm like it is trying to kick on
Did you connect the jumper wire to rc---rh on the thermostat? ... Air Conditioners
Coleman mobile home furnace Model #7966-756 will not turn on. The pilot light is lit, there is power coming to the step-down transformer inside the furnace. The reset switch is in the right position. It worked fine when i turned it off last spring, just wont start back up now. The blower fan will not even come on when i switch it from the auto position to the on position on the thermostat. Any ideas?
I had a similier problem, Check your neutral ground? also alot of power companies will come out and do a basic check of the voltages going to the furnace, and can offer advice for free. ... Coleman Air Conditioners
Ruud achiever 10 seer air conditioner wont turn on...thermostat kicks on and i feel air but outside unit wont turn on..what should i check??
Have you check the outside breaker box? If thats not it then its probably the contactor. ... Ruud UBHC Air Conditioner
Ruud Silhouette II furnace: comes on and runs for as long as it wants, then turns off. Sometimes turns off at pre-set temp, other times just when it wants. May turn on again, behave well for several cycles, or for 20 minutes. When I get too cold, I go out, downstairs, and thump it near the fan. Starts right up, runs for as long as it chooses. Nearly least energy-efficient kind, v. frustrating. Had trouble-shooter out a few years ago, couldn't find anything. An intermittent short?
Hi ruby. Begin by installing a new thermostat. Preferably one that allows you to program weekday and weekend temps. separately. Joe ... Ruud UBHC Air Conditioner
Ruud air to air heatpump intertherm propane furnace honeywell th5220d non programable thermostate.fan on furnace will not turn off in aux.mode even though the furnace heat kicks on and off. thank you for any info.Ray
Make sure fan relay is wired correctly (G) wire. Ensure the fan on therm is not on, it should be on Auto or off. \015\012\015\012If your furnace is short cycling because it has to keep heating your home, the delay in the control board m ... Intertherm Air Conditioners
Ruud Furnace won't turn on
Take of the access panel on the furnace and look for a wiring diagram either on the back of the panel or inside the housing. There will be a diagnostic chart on it that will give you a hint what 2 flashes mean. I think it is a "no Ignition" code. ... Air Conditioners
Lux tx500e fan flashes wont turn on furnace
... Air Conditioners
Coleman 7900 gas furnace/central ac, was working fine, now blower wont come on, it tries but turns real slow then stops, i took it out and bench tested the motor andit works fine, put it back in the furnace it wont work. What do i need to replace??????
Motor run capacitor. If problem is intermittent, try wiggling wires from motor to capacitor to check for broken wires. Motor might seem to work ok with no load on bench but it has no real power. The power to really spin the motor under load comes ... Coleman Air Conditioners
I have a Tempstar 9000 airconditioning unit and while I was weed wacking I accidently cut a wire to the unit. I replaced the wire but now the unit wont turn on and also my furnace blower wont work even in the "on" position. I have a energy saver unit attched to the a/c unit as well. One wire connects to the a/c unit and the other to the energy saver. If I push the connector on the unit with the panel off the unit will run. Cansomeone tell me how to connect those four wires?
Hello TLOEKS You blew the transformer FUSE inside the blower unit! It should be a 5amp blade fuse like the one that goes in a car.It is located at the curcit board at the blower compartment.Replace that to restore low voltage power and every thing wi ... Air Conditioners
Blower motor on my Ruud furnace won't turn on when the a/c is on also won't turn on manually
You need to buy a new fan motor. If you could have turned the fan with your hand all you would have needed would have been a capacitor. If your filter is always dirty or the a coil is dirty will shorten the life of a fan motor. Just for things to ... Ruud UBHC Air Conditioner
The blower in my Ruud gas furnace won't shut off. It just runs and runs. The thermostat is set to "off" and the fan switch is set to "auto". We haven't used the furnace or AC the past few months since we haven't needed it, so it's been in the off position. Then yesterday out of nowhere the blower randomly fired up and hasn't turned off since. It just runs and runs until I kill it at the breaker. The thermostat is about two years old so it's fairly new. I replaced its batteries and that didn't
I'm not sure what setup your unit has but the fan relay sound like it is bad. If your blower connects to a circuit board then the board could be bad. Different units use different ways to control the fan. Some use a relay like I mentioned. Some use t ... Ruud UAKA037 Air Conditioner
Central air just stopped running, was running all day. I turned down the thermostat about an hour ago and I heard it come on. I noticed it wasn't running just a little while ago. Looked an the thermostat says it is 78 while the aircon is set for 72. It wont come back on I tried resting the thermostat and checking the breakers. I even switched the furnace off on the side. The furnace is about 30 years old...
Possible you have a bad contactor switch.. Have a tech look at this since it is dangerous due to high voltage and age of unit\015\012\015\012Good Luck\015\012\015\012Dave ... Air Conditioners
Furnace is a York Model#p4ugd12n09001a probably installed around 1991. The air condition was working fine. couple of days ago nothing was working. Blower wont tun on, air conditioning unit wont turn on. I did have the fan on the on position on the thermostat so it was always on until it stopped.
Probably a bad low voltage transformer. ... Air Conditioners
For ruud achiever 10 ac unit uaka-030jaz. Unit was working fine saturday...sunday we noticed air was not cold anymore. I have checked all my breakers, put a new battery in the thermostat, cleaned the filter on the furnace unit, and opened the exterior unit to see it the relay was burned( appears ok as long i understand which part is the relay.). When we turn on the ac the furnace unit in the attic will come on and blow air..however it never gets cold and nothing in the outside unit appears to co
Hi, the problem is in the outdoor unit if the indoor unit comes on and is blowing air. At the unit, you will have a disconnect box, 220 volts. Inside there will be 2- fuses. If you can't see them its because they are behind the plastic cover. You may ... Air Conditioners
I have a ruud achiever 90 plus furnace and the orange light blinks when the furnace is igniting and then everything turns off. Then it just blows cool air. HELP
Here is a website that may or may not help, Timhttp://arnoldservice.com/Troubleshooting_Heating_Problems.htm ... Ruud Air Conditioners
FURNACE OR AC WONT TURN ON
To see if it is the t-stat or the system you can unwire the entire t-stat and jump out the wires. never touch the blue to any other wire or you will blow the low voltage fuse on new board. if you jump red to yellow and your condensing unit cycles on ... Intertherm Air Conditioners
Air conditioning wont turn on either will the furnace.
Not being there this hard one! but i can tell you that the thermostat controls both heat and cool. ... Air Conditioners
Ruud urgh07e36jkr heater wont turn on
Well I checked and the pilot would light and then go off right away and repeat.I jumped the 24v terminal to the pv pilot valve terminal on the ignition module and the main burner lit up. I then disconnected the spark igniter and the burner shut off a ... Ruud UAMB Air Conditioner
Electric furnace wont turn on in auto mode
... Air Conditioners
Ruud achiever 90 plus gas furnace not turning on
Remove and clean the drain trap and make sure the drain tubes are clear.\015\012It sounds like the water may be building up in your drain lines.\015\012Hope this helps.\015\012Matt ... Ruud UBHC Air Conditioner
My fan outside will not turn off. I have a Ruud Achiever 10 unit. I cleaned the coils on the unit outside and the filter for the furnace. The unit does cool.
Is the compressor also running or just the fan? If both are running, you've probably got a freon leak and the system isn't cooling properly so it runs continuously trying to reach the thermostat set-point.\015\012\015\012If only the fan i ... Ruud Matching Split Air Conditioner
Goodman gmp0753 wont turn on condenser. The thermostat yellow wire is not connected to the unit. Does this play a part in my problem and where does this wire connect inside the furnace.
The yellow wire is used to run your air cond. inside the air handler at the transfomer should be a row of wires that have r, c , w, G, Y hook the yellow wire to the y terminal. ... Air Conditioners
For the ruud high efficiency furnace model # ugfd-o6emcks i need to know if i need to flip any of the dip switches if i want to run 2 stage from the stat. I have everything else i need just need to know if any of the dip switches need to be turned on?
... Ruud Air Conditioners
I have a ruud 90 plus achiever gas horizontal furnace. the unit will run once i turn the thermostat off then on. it will cycle a few times go off and then will not come on. any suggestions?
Sounds like it could be a dirty or bad flame sensor.When the burner lights ,there is a flame sensor in the flame and it is suppose to sense the flame and send a signal back to the control board which will keep the gas valve open, if it gets dir ... Ruud UBHC Air Conditioner
I have an coleman evcon furnace when i turn a/c on the outside unit will run but the inside wont run
Put the just the fan on turn off the ac and the heat and just fan on make sure the blower motor works cause thats really the only thing you utilize from the furnace in the summer and let me know\015\012then if so does your heat work fine ... Air Conditioners