Having problems with your Air Conditioners ?
Central air conditioner doesn't turn on... Any suggestions?
Both the inside air handler and outside unit would not come on. After disconnecting the thermostat and reconnecting it and setting it on cool both units came back on. Is this an indication of a bad thermostat or is it possible it reset.
If the compressor turns off and won?t come back on during a very hot day, the unit may have built up a high "head" pressure and the high-pressure limit switch may have tripped. This is usually located right inside the access panel on the compressor unit. Simply push the button to return it to operation.\015\012\015\012If your central air conditioner doesn't go on automatically:\015\012\015\0121) Be sure the thermostat is set to "cool" and set below room temperature.\015\012\015\0122) A central air conditioner should be on a dedicated 240-volt circuit; check the main electrical panel and any secondary circuit panels for a tripped breaker or blown fuse. If you find the problem here, reset the breaker or replace the fuse.\015\012\015\0123) Make sure the furnace power switch is turned on and that the outdoor condenser's power switch, mounted on the outdoor unit, hasn't been shut off. Also be sure the 240-volt disconnect next to the compressor (in a metal box, usually mounted on the house wall) hasn't been shut off.\015\012\015\0124) Turn off the power to the air conditioner and check the thermostat.\015\012\015\0125) Remove the thermostat's cover and unscrew the wire from the Y terminal.\015\012\015\0126) Turn the power back on.\015\012\015\0127) Holding the wire by its insulation, touch the bare end to the R terminal and hold it there for about 2 minutes. If the compressor kicks on, the thermostat is faulty; replace it or call an air conditioning technician. If the compressor doesn't go on when you hold the two wires together, turn the power back off and call a service technician.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
My central cooling system does not work. Every things is working accept a compressor. When I turn on the cooling system the compressor makes strange nose and after one minute it turns off, but fan kips continue to work. Do you have any suggestions for me? Thank you Model # of my air conditioner is CCU10A42A-1
Compressor overload on the compressor ... Air Conditioners
Central air conditioner doesn't turn on... Any suggestions?
Both the inside air handler and outside unit would not come on. After disconnecting the thermostat and reconnecting it and setting it on cool both units came back on. Is this an indication of a bad thermostat or is it possible it reset. ... Haier Energy Star ESA3183 Air Conditioner
CENTRAL AIR My central air conditioner blower won't turn off and the A/C won't turn on, can anyone help me with this please?????
Many low voltage circuits "flag" you when there is a problem by running the fan when the low voltage circuit is broken by a blown fuse, open high temperature safety or a similar interruption in power. A qualified service technician can tell what the ... Air Conditioners
My central air conditioner turns on and only hums but fan does not turn and does not cool what could be the problem?
... Air Conditioners
We just turned on our central air conditioner last night. today the temp of the house was 80 degrees. someone in the household placed the tempature on 70 degrees cool on auto. we have not felt any air coming out of the vents. the central air unit is running. any idea why this happened. our thermstat is not programmable.
Did you hear the indoor unit running (the fan blowing)? If so, there's a good chance that either the filter is plugged or more likely, the evaporator coil is iced up and preventing any air from flowing into the dwelling.\015\012\015\012T ... Air Conditioners
I just purchased a house that has a Goldstar air conditioner. I turned it on yesterday, and it worked fine. I left the house for an hour. When I came home the air was no longer on. I turned it off and tried to turn it back on and unplugged it and flipped the circuit breakers, but it still won't come on. Any suggestions?
... Goldstar R1804 Air Conditioner
Air conditioner unit outside, fan not going but air is coming out of the vents. The thermostat is on 50 degrees. If it is shut off for a while and turned back on it will turn on but after and hour it will shut off. Sometimes it will run a day and then shut off but will not go on again. Any suggestions?
Is the fan out side running when you are getting cool air? IF so check the out door coill is it clean, If not the fan could be over heating because it is pulling to hard. you should be able to feel the air 2' above the unit. ... Goodman CKL24AR24 Air Conditioner
My portable air conditioner Model # AP077R, is not functioning correctly. I just opened it last night and now it is malfunctioning. Once plugged in, it will act as if it is cycling between blowing air, then stopping, and starting again. I can not turn it on or off. It runs through this cycle by itself and the only way to stop it is to turn it off. Do you have any suggestions, or is it just defective?
Yes it sounds defective from fatory and should be exchanged. ... Amana Air Conditioners
I have a Haier HPRBO7XC7 portable air conditioner that isn't working properly. When I turn the air conditioning mode on, the cooling unit seems to turn on, but then stops after about a minute or so, and the fan just keeps running. The unit is only about a year old. I purchased it last summer, it worked fine and then when I pulled it out the other day, it had this problem. Any suggestions?
... Haier Air Conditioners
I have a Samsung Biotech plus air conditioner - Model SC12ZAB. When the system is turned on, all the lights on the control panel light up and it is not possible to select any of the 5 sway options to operate the air conditioner. Also, the unit does not repond to the remote control. Any suggestions?
Warranty? go that route. Id unplug at least a minute see if it's brain will reset. With these new fangled computerized machines, one needs to be a specialist's specialist. Hopefully you have your owner's manual, it has a troubleshooting section, ... Samsung Air Conditioners
My nec RSC3337 air conditioner is not taking the remote signal. the battery is good and i have already tried using the force start holding it for more than 3 sec. i am getting the beep but still its not taking any respond from the remote. i have been switching it on and off using the force button. but inspite of tht when i turn it off it doesnt turn off fully i have to use the remote to turn it off. in other words i have to first turn it off using the force button to turn it off and the the off
Try unplugging the main unit for a couple of hours; it may have just locked up. ... Air Conditioners
Hi I have a Lennox heat and air conditioner roof top on my unit. What's happening is,the heat turns on for a about 10 minutes then shuts off, the only way to turn it back on is to turn off the thermostat, then turn it back on, but will keep doing the same. Oh and one other thing, the filter warning is showing on the thermostat, could it be as simple as changing the filters? Any suggestions anyone?
You are right, you must change the filters, since it isno longer working normally. May this help you. ... Air Conditioners
I have a Fedders A1A10W2B in wall Air Conditioner. Was working fine last year. Turn unit on last night and ran the fan for a few then when I put in cool no cold air will come out. It will make this humming sound like it wanted to, but the air was just regular air. Any suggestions? Does it need freon?
... Fedders A1A10W2B Air Conditioner
I have a GE central air conditioner model
If you are talking about the indoor fan it is probably a bad capacitor. Replace the fan motor capacitor. And YES, if the fan motor needs replacing too, you can DO-IT-YOURSELF. ... General Electric Air Conditioners
My air conditioner doesnt blow cold air turns on and blows but the air flow seems to be only a little house gets hotter and muggy
This is most commonly cause by a lack of freon in the system. Unfortunately, the only solution to that is to call your local A/C company and have a certified technician come and charge your system. The reason you need to call a professional is beca ... Air Conditioners
Air conditioner/furnace was working for the past few months. Came home today at it is at 81 degrees, although my set temperature was set at 72 degrees. Temperature is rising to 83 degrees and I can't figure out why the air conditioner won't run properly. I turned the fan on from auto to on and it's blowing warm air. The default scree on reads the current temperature at 82 degrees with a circle and snow flake above it and an downward arrow where the word room is written. Any suggestions? I t
Check outside breakers. Open up outside panel and see if contactor is pulled in. If so you have a voltage problem or a bad capacitor. Sometimes a wire burns off. So look for this. If you have a float switch on the inside unit it may be tripped. Stopp ... Air Conditioners
I have a honeywell pro 2000 programmable thermostat which controls an enerzone ahc 31-18 series water source air handler with heating and cooling coils built in. This therostat and heater worked fine all winter. Last week i had a air conditioner stalled and connected to the air handler and the AC worked for one day. When i tried to turn on the AC yesterday, the fan would not come on for either AC or heat. any troubleshooting suggestions? thanks ... Donald
... Air Conditioners
COLMAN TSR I JUST BOUGHT A HONDA EU 3000 IS THAT I WAS TOLD SHOULD RUN MY AIR CONDITIONER WITCH IT DOES FINE UNTIL THE COMPRESSOR STARTS CYCLING. WHEN THE COMPRESSOR TRIES TO TURN BACK ON IT TRIPS THE OVERLOAD ALARM. I HOOKED IT TO THE HOUSE AND IT DOESN'T TRIP THE CIRCUIT BUT WHEN IT TRIES TO CYCLE THE FAN DIES ALMOST ALL THE WAY OUT FOR ABOUT 5 TO 10 SECONDS THEN THE FAN STARTS RUNNING OK AGAIN BUT NO COLD AIR FOR ABOUT 30 SECONDS THEN IT CLICKS FAN DOESNT CHANGE AND COLD AIR RESUMES. THAT LAS
3000 Watts is a little short on the power necessary for the compressor to restart. When it compressor starts it may draw 27 amps or more for a split second. 3000 / 120 = 25 amps. when the fan slows down it is telling you the voltage has dropped and i ... Coleman Mach 15 Air Conditioner
We have a slim heater/ air conditioner on our wall. It's been in airconditioning mode for the summer. I'm having trouble 1 . it shuts off within seconds of turning it on. I've tried to cancle the timer. Lost the manual. 2. I cant get the fan to blow warm air, the blade to even rotate but it works with cold air!!!ouff... ....the remote is on heat ....temp says 74 on both wall and remote mdl # LMN120HE suggestions?!? We're cold.....
This is a tippical heatpump problem. get the revers valve unstuck. energise the coil to the valve, on and off. make sure the power is on to the coil.(HEATING MODE AT FULL TEMP). if you are not electrical minded leave it be. get someone with electrica ... Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Goodman air conditioner model #PC036-1a; when you put on heat the unit kicks on and blows out air with no problems but when you try to turn ac on, you can hear the motor click on like it's trying to start but no air blows out of the vents. thought it might be the relay switch? any suggestions
Try replacing the control board most the time its a relay stuck open for high speed on your fan ... Goodman Air Conditioners
Have a Amana a/c heater central furnace. Model number PGA30R0452A. The a/c part works fine. The heater part does not turn on sometimes. We have to keep turning it on and off to get to work. No matter what you hear a slight humming when we turn it on just it doesn't always blow air out of the vents. It also does not always kick back on once the temp. has dropped and should start heating the house again. We have programmable thermostat. Any suggestions to whats broken or breaking. My husband woul
When you change from cooling to heating the fan will not come on immediately. A solenoid valve is energized (check that it is working) and operates a reverse valve, changing the gas flow in the system. It takes a few minutes for the system to build u ... Air Conditioners
Central air conditioner will not turn on at all.
I understand this to be a heat pump. Check your thermostat settings, and the filters. And make sure a breaker isn't tripped. ... Carrier Air Conditioners
Kelvinator Split System Air Conditioner not turning on.
On some remotes there is a reset button which is pressed by using the nib of a pen. Or if this does not work you should look under the cover for a manual button, most units have one, and see if the aircon responds. I suspect your remote sensor is fau ... Air Conditioners
Just bought a used 1987 Real-Lite truck camper. The roof air unit is Dometic as well as the LP/AC refrigerator. When turned to "cool" the air conditioner really draws down, dims the lights, and eventually blows the home AC breakers. It works fine on blower fan only but as soon as I engage the "cool" settings, big brown out. The fridge doesn't work at all. I'm in the Nashville area. Suggestions
To start with, if it's plugged in to a 15 amp breaker, and extension cord, the compressor starting up may just be enough to trip the breaker. It will draw close to 15 amps on start-up of compressor, and if there is a light extension cord used to plug ... Dometic Rooftop RV Air Conditioner
I have a Sharp CV10NH Portable Air Conditioner with the same problem as posted by gtkermit on Jun 08, 2010: works fine for a few minutes then compressor turns off and fan continues for a few minutes then compressor kicks in again and cools for a few minutes (cycles about every 5 minutes perhaps.) I have followed all suggestions on page 30 of the manual (as well as the different options for venting, etc.) ms-shop suggested that the thermostat needs to be replaced. How do i do this? Thank you!
Hello,The problem could be the thermostat, and any of the following compressor cycling for every few minutes\015\012could be over load for the compressor, dirty condenser coils need \015\012cleaning, To check \015\012the compressor\015\01 ... Sharp CV10NH Air Conditioner