Having problems with your Air Conditioners ?
Rudd heatpump doesn't cool
Hi, \015\012 Is the condenser fan running? If not, Check the circuit breaker inside the house and the quick disconnect at the condensing unit. Making sure the power is off, check for any bugs in the contactor. If it is running, check to see if there are any resets on a high pressure switch or control board in the condenser. Check the compressor capacitors and see if they are leaking oil or swelled up. are there any burned wires? Is the compressor hot? If the fan is running and the compressor is not hot it is probably off on Low Pressure and needs charged by a licensed Air Cond Tech. Hope I have helped. Let me know.\015\012kstfas
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Rudd heatpump doesn't cool
Hi, \015\012 Is the condenser fan running? If not, Check the circuit breaker inside the house and the quick disconnect at the condensing unit. Making sure the power is off, check for any bugs in the contactor. If it is running, check to see if there ... Ruud Matching Split Air Conditioner
My ac unit doesnt cool anymore. I've cleaned the filter and its spotless but cool air doesnt come out at all, its like an expensive fan. Is it out of frion?
May be your compressor, a cap or freon ... Danby DPAC7008 Air Conditioner
I have recently purchased a Dimplex GDC18RBA portable airconditioner and it blows out cool air, however it doesnt cool down the room and the thermostat temp doesnt go down to the temperature I set it at. I had it on all night long last night and the lowest temperature it got to was 29 degrees. Please help
The air is cool but doesn't seem cold enough and does cool the room to specified temperature ,then check the following:--\015\012 \015\012If the air doesn't seem cool enough it is ... Air Conditioners
Doesnt cool on cool side but it will cool if its on heat side
Wire crossed.call a service tech ... Coleman Mach 15 Air Conditioner
Everstar mpk10cr grinding compressor I think.... Fan works fine, will kick into cool mode (elevated fan level) for a few seconds then it sounds like the compressor has a loose mount or something... sometimes it rattles for a few minutes (and cools) but sometimes it shuts the rattling off as fast as it starts and doesnt really ''cool'' or dehumidify.... Some days its works fine all day, others it just never really gets its ''**** together'' so to speak... Can users recharge the coolant themselve
Hi, I hear you , you have to keep her happy and cool!! First of all, no you can't buy R-22 unless you are a contractor and you have a certification card showing you are qualified to use freon. This is not your problem from what you are saying. If thi ... Air Conditioners
Doesnt cool small bedroom with doors shut. I have
It should freeze that room with 9000btu do you hear the compressor turning on or is it blowing jus air? also helps if you switch the air intake to recirculate the room air rather than intaking the air from outside ... Maytag Portable Air Conditioner M6P09S2A
I have a maytag nmpeb08f2a portable ac, just started it up for the season. cleaned the filters and coils by wiping down . I also emptied bottom resevior. Im not getting cold air when on cool setting, tried lowering temp all the way. when i turn it on it will be cold for a short time, doesnt fell cold like befor, the temp will go down maybe 1 degree then, no more cool air. can i add refrigerant to this unit?
Frank, refrigerant is what it needs, but it should be done by a pro. Unless you have experience with this sort of thing, it's not a DIY project, ... Maytag Portable Air Conditioner M6P09S2A
We have a gem cool air conditioning unit in our office but no manual. It doesnt seem to be cooling at all (it was installed last week and it was working fine then) and we are not sure what settings we are getting wrong. Is there somewhere online where we can find the manuals for this brand?
... Air Conditioners
I have whirlpool magicool window ac. Now a days it is not cooling. Where the temperation blinks now a dot (.) is blinking after every 5 minutes and then ac doesnt cool - rajesh
You need to change the filter and clean the coil behind the filter. If the a/c cannot breathe it will cause the symptoms that you are describing. The coil at the front of the a/c may be clogged and the system isn't recieving thew airflow needed to ... Air Conditioners
I recently bought a 4 ton 14.5 SEER Rudd Spilt system using R-410 and matching Rudd furnace. This system replaced a Lennox 10 SEER 4 ton unit. Now that it has gotten hot in Baton Rouge LA 90-93 degrees. I have a programmable thermostat see bottom. It takes the one hour to drop the temp. 1 degree so starting at 5:00pm the unit runs non stop until 11:30 at night. The Lennox was about 3 times better and it was 15 years old. The installer told me all high SEER units take longer to cool in comp
Sounds like the Unit might be low on charge.But without correct readings not sure.\015\012The new unit with 410 will actually cool better due to higher boiling point temp. of freon type.Poor air circulation could also cause problem.Such as dirt ... Air Conditioners
My Trailer AC doesnt cool below 75 degrees. I feel no differnce between the coldest setting on AC than on the Fan cycle. I cannot hear the cooling system kick on at all.
It should read 24v not 12v!!!!! Check your sub base on the t-stat. Voltmeter set on volts, touch R to C and get 24 volts if no common to the C then touch R to G which is the Indoor Fan Motor! If the Indoor fan is blowing air out the vents you are get ... Dometic 57915531 Air Conditioner
I set the thermostat to 70 degrees but it doesnt cool down to 70, it seems that the temp in the house only rises, instead of cools down.
Setting Unit at 70* ? and not cooler ( dropping temp in the house ) Question ? does temp dop at all, if so the Unit maybe unsized, if the temps are going up then the unit is not working at all - maybe just the fan is running. If this is a split unit ... Air Conditioners
My 2001 VW jetta VR6 heating and cooling are not working. Sometimes if I turn the AC on I will get a little bit of cool air but it wont blow hard, but most of the time it doesnt work the heating is the same way.
... Air Conditioners
Central air conditoner unit doesnt blow cool air into home has some ice on the inlet heat and cooling lines going into the central air unit
Change the furnace filter. Make sure you use a cheap one when air conditioning, as the better ones restrict airflow when they filter out so much stuff and then plug up, not allowing enough air to pass over the cooling coil in the furnace's air plenu ... Carrier Air Conditioners
My mini split turns on but is not cooling. It comes and goes... sometimes it cools, and the majority of time it doesnt. Plus, is leaking water. I live in an island and is hot! I need help!
With out looking at it, I can give you some ideas that could cause these problems. I need to know where the water is coming from? If it is leaking on the inside, this narrows it down some. It sounds to me that the evap. coil is icing up which the uni ... LG LS-L1210CL Mini Split Air Conditioner
I have a problem with split-type ac unit, when the unit stops due to cooling, the unit doesnt turn on to cool operate again. I have to set the control to start the unit again. Someone recommends me to change the capacitor of the outdoor control unit. Or maybe I have to replace the a/c unit?
First of all I would change out the thermostat since you say you have to turn the unit on at each use. The capacitors only assist in the start of the compressor and fan. You main issue seems to be the activation after the unit has been off. I thin ... Carrier BCA101R Air Conditioner
My Ac do not cool enouhg, even it doesnt cool anything, i have my windows close and there is no equipment that produce heat!
Hi Cafe, \015\012Ensure that the the discharge (hot air) is properly routed outside. Take temperature readings of the intake air (room air entering the unit) and the outtake air (cold air coming out of the unit). If the temperature difference i ... Midea MPM-08CR-BB4 Portable Air Conditioner
I have a Trane Xe1200 heatpump with aux heat strip, currently it will cool the house down, however, after it does this, the compressor continues to run unless you shut off the thermostat. Also, if yo
... Air Conditioners
Rudd heatpump compressor runs outside fan dose
I don't think the fan on it' own crates the problem. Could you find out what should be and what actually is the flow through it. If you needed <!-- MOJAIZBA.COM LINK CODE START -->\015\012<a rel='nofollow' href="http://mojaizba.com/convert-u ... Ruud Air Conditioners
Doesnt cool as well as have been told
There are allot of conditions that affect the cooling, outdoor humidity, if it is between 10 and 15% humidity, then it should work well, anything above 30% outdoor humidity, it won't work. That is just nature, but duct sizing or is it a single drop? ... Mastercool 67680 Evaporative Cooler Air Conditioner
Doesnt cool room as in prev years
Yes the side vents need to be outside the window and if they aren't - the unit will not cool correctly.\015\012\015\012Hope this helps. ... Goldstar WG5000 Air Conditioner
Heatpump made a bang and now doesnt heat
... Panasonic KE18NKU Heat Pump Wall Mounted Ductless Mini Split System - 17,500 BT
HAVE A BRAND NEW RUUD 13AJA36A01757 UNIT DOESNT SEEM TO COOL HOUSE AT ALL WHAT TO DO
... Ruud 13AJA36A01757 13 SEER DRY-22 3 Ton Air Conditioning Unit
Coleman outside mounted air conditioner in park model doesnt cool sufficiently
... Coleman Air Conditioners
My rinnai E110CN doesnt stay hot, it fluctuates warm and cool. Any ideas other than the mixing valve?
... Rinnai E110CN 110K BTU Condensing Boiler