Having problems with your Air Conditioners ?
Air condition freezing up
Make sure the condensate drain is clean and clear of any debris. With the indoor unit off, Remove the inspection panel and pour a gallon mixture of 10% Bleach to Water solution in the drain pan. Do not overflow the pan but check to make sure there is flow to the outside or drain. Clean out the drain hose if you have to. \015\012A freezing coil is a sign of either not enough air going across it or not enough charge in the system. Check to make sure all of the return air vents as well as supply vents are in full open and unrestricted. If they are, you will need to have the charge checked. If this turns out good, have your technician install an anti-freeze kit. This kit will temporarly turn off the compressor unit for a short period when the sensor in the kit experiences a freezing condition. Then after a bit, it will turn on the compressor. It may not cool as much as it was, but it may get you thru. \015\012\015\012Good Luck!
Have an HVAC tech recover the refrigerant from the unit an recyle it during the recovery. Remove any old filter dryers installed on the unit and replace with a new one! YES! Braze in new ones! Pull a triple vacume on this sytem down to 500 microns to insure all non-condensables are evacuated from the system. Weight the charge of refrigerant back in and set by superheat readings from the evaporator coil to the compressor! majic number is 40f evap outlet plus 12f to make it around 52-55 at the compressor inlet. Your problem has been restrictions in the refrigeration cycle either in capillary tube with orfice for metering device or a TXV getting cloged with ****! Hope this gets it solved for you!
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
My air condition inside unit seems to be freezing up and the air stops blowing through the vents after I turn it off it sounds like ice melting. after a few hours I can turn it back on ,it will blow throuh the vents again there is a fan on yhe front of the inside unit it is making noise. is that a exhaust vent not the one that blows air through the vents. how can I fix this myself
When does it make the noise, when on AC or heat?? 2 things if the fan is on the ac unit itself that's not the one that blows air thorugh your vents, if its the one inside the furnace that is the one that blows air through your vents, but remember th ... Goodman CKL60AR60 Air Conditioner
1. The air conditioning unit is freezing up 2. The motor is on the highest mode and the thermastat is set on 10 and the cool air is not kicking in. Please advise what we should do.
Have a service tech come out your freon leveals could be low ... Air Conditioners
Air condition freezing up
Make sure the condensate drain is clean and clear of any debris. With the indoor unit off, Remove the inspection panel and pour a gallon mixture of 10% Bleach to Water solution in the drain pan. Do not overflow the pan but check to make sure there is ... Air Conditioners
Coils on home air conditioning unit keep freezing up
How humid is it when you run it? ... Air Conditioners
Freezing up on goodman air condition cple36-1
Hello, freezing up is either a airflow problem such as dirty filter, dirty evap coil, dirty blower wheel, wewk blower motor ot a low refrigerant charge. ... Air Conditioners
Air condition unit freezes up
Hamtonbay window a/c fan blower loud nosie when unint modelhblg 1800 ... Hampton Bay HBLG5004 Air Conditioner
I have a goodman unit aruf036-00a-1a, the coil freezes and no air conditioning comes out. I am told that Goodman has a problem with leaking coils. The unit is 6 years old.
... Goodman Air Conditioners
Our Ruud Air Conditioning coils keep freezing up. We have already had freon added once.That tech said we would probably have to replace the whole unit. Does that seem right?
It is possible that the compressor is going out and causing the problem, but not that common. Your evaporator coil freezing up can be caused by a couple of things. The most common is a dirty/clogged filter, dirty/clogged coil. This will cause less ai ... Air Conditioners
With unit set to air conditioning, the controller board will not turn on the blower motor and the cooling coil freezes up. McNutt tells me the controller board is kaput and they want $550 for it. In the meantime they have jumpered over the controller so the blower runs constantly. Was hoping someone might be able to tell me where to get it for less. It is HSCI Furnace Controller For Use With All Gasses 1012-940, model HK42FZ011
? need more info like make model and serial numbers ... Air Conditioners
Why is my air conditioning unit keeps freezing up
Low ambient outside temperatures can cause this problem if you are running your system with the fan in the automatic mode. When the fan cycles with the temperature ice built up in the cooling cycle has no means of defrost. Set your fan control to on. ... Air Conditioners
My air conditioning started doing some noises and got freeze. I called the technician and he put some gas. But after few days, the compressor stopped working. What could be the reason for this to happened?
GUIDE ... Air Conditioners
Air condition unit will not cool and the coils freeze up in just a few min.
Is the inside fan running properly? Typically if the condensor outside is working, but the fan inside is not, the coils will freeze up quickly. For the system to work properly, you need to be blowing warmer air over the coils inside the house- that ... Intertherm Air Conditioners
During air condition mode fan does not run unit freezes up and there is a red flashing light on the circuit control board. The board # is GMP 125-5. The outside compressor work normally.
Dear tomsandi,\015\012 Either the fan motor is burnt out or it is not getting the power supply, hence the fan is not working. Since there is no air passing through the evaporator the cooling is not taken off fron the co ... Air Conditioners
Our air conditioning was working during the day. when one family member turned the air up from 72 to 75 she saw the screen process what she wanted and walked away. when another family member went to turn it down, the screen was off. i have a honeywell visionPRO thermastat but no air conditioning at the moment. is my air conditioning not working because the honeywell theromastat needs to be trouble shot or is it not working because the machine that produces the air conditioning itself not wor
Open the thermostat and look for batteries, 3 AAhttp://www.heater-home.com/photos/2129-5b.jpghttp://www.heater-home.com/manuals/th8321u1006manual.pdf ... Honeywell Air Conditioners
Hello! can you help me.I have air condition GREE splite system. SOme days ago when he start to work( i put heating, to warm) in some minutes stops and write on the air condition (up, not in control) H 1 Can you explane ,what it is? I have 2 air condition in different rooms one bigger then other and they make the same Thank you Yulia
Also have you cleaned your filters? ... Air Conditioners
I have a GE "AS1AH09DWF02" air condition and the remote control stop working... I have change batteries and it shows the display ok but it can't turn on the air condition. The air condition has a green light which is winking! What can I do please?
... GE AJCQ08ACB Air Conditioner
The haier is freezing up we bought it last year and its already freezing .. we cleaned the filter and dont know where the evaporator is but no cool air is coming through alot of ice on it though
Unit is freezing over and i just cleaned it ... Haier HWR06XC5 Wall/Window Air Conditioner
Kelvinator 90plus 60,000 furnace heat good. pushes little air on air conditioning. checked filter--clean- checked charge in condensing unit. ok. 2 years old. never has pushed air conditioning at all. barley trickles out of the supply air registers. could the fan not be on high speed?
The air flow you feel coming out of the vents is good on heat but not when the ac is running? ... Air Conditioners
Hi My Danby 6000 BTU window air condition is not cooling. I set thermostat to maximum cooler level as 8 but still not cooling room. I clean all the dust with wire brush. Fan is working fine and I can feel lots of air comming through the air condition but no cool air.
... Danby DAC6003D Air Conditioner
Where are the air filters located on my 2005 Winnebago Journey 34H with Coleman Mach basement air conditioning unit (True Air residential air conditioning). I need to change them.
The filter is under the bed in rear. ... Coleman Mach 15 Air Conditioner
I have a 5 ton 11 seer heat pump, i am going to buy a new regular air conditioner, 5 ton.. The air conditioning salesman said i would have to put in a heatpump in by fl. power&light and port saint lucie code, that i cann't put a regular air conditioning in.. Please let me know .. Paul Mokry
This is nonsense, and completely false. I would "Recommend" that you have an electric heater coil(10kw or so) equipped on your new unit for the few days that you might want to turn on the heat. ... Air Conditioners
Audi A4 2002 2.5tdi V6. air conditioning failed Garage put in new compressor and regassed - still not right regassesd -still not right Found oil from the air conditioning in the system, cleaned out and regassed - better but still not right, takes time to get down to cold air and warms up when rev's are down. Any ideas?
... Air Conditioners
Hi, there is a Ductless LG Model # LA180CP that has freez up problem. Sometimes it freez up after 3 days working and some times after couple of hours working. Freez up start from indoor unit. Average of super heat is 10, but it is changing all time between 6-15. suction line Temp 45F, Discharge 53F, On Gage 35F, Supply Air Temp 8.2C and Return Air Temp is 22C. What do you think about this issue? THanks
What refig and where are the pressures. freeze up is always low charge or lack of air flow and always occurs at the evap. Once it starts and you loose surface area you have to defrost manually ... Air Conditioners
Plentiun air conditioning coils are icing up after running in cooling mode. is there a timer relay circuit in the air conditioning unit that turns the cooling pump on and off to keep the moisture on the coils from turning to solid ice and stoping air flow?
Ice forming can be the results of dirty filter, dirty coil, low refrigerant charge. ... Carrier 38CKC036 Air Conditioner
My air conditioner lines keep freezing up.
You have a blockabe in the distributor tubing which will need a professional to sort out. ... Air Conditioners