Having problems with your Air Conditioners ?
Ruud heat pump
Hello do you have a Soleus KFR-18w/d mini/split
If so I have the same problem
If so I have the same problem
THE LAST THING TO SUSPECT IS "LOW ON REFRIGERANT". MAIN CAUSES IN ORDER: "OVERCHARGED",DIRTY FILTER, DIRTY COIL, BLOWER MOTOR IS HEATING-UP AND SHUTTING OFF ON INTERNAL OVERLOAD PROTECTOR, ANY THING THAT MAY BE RESTRICTING AIR FLOW IN THE AIR HANDLER, NON-CONDESEBALES, LOW REFRIGERANT. I FIND ON MOST LOW CHARGED UNIT THE "SUCTION" LINE IS WARM AND THE EVAPORATOR COIL IS FROSTED. YOU ONLY GET ICE BACK ON THAT LINE ON THE COMPRESSOR IF YOU VISUALLY LOOK AT THE EVAPORATOR COIL.\015\012A COIL THAT IS ICED UP IS LACK OF AIR OR A OVERCHARGE. A LOW SECTION OF SOLID ICE INDICATES A LOW CHARGE.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Heat pump goes str8 to heating strips compressor does not run in heat mode pump was manufactured in 03 installed in 07 and has sat dormant till now could it be wired wrong it is a ruud split unit with digital non-programable 2-stage heat and cool t-stat
I think that you have the right idea. The wiring is probably wrong. If you can trace the low voltage wires to the air handler. make sure that the Y1 wire on the t-stat is going to Y1 on the hair handler and then to the condenser. The Y2 wire should b ... Air Conditioners
Aux heat always comes on in heating (Ruud heat pump)
What type of system is it, if it's it Rheem the o/b needs to be set for B, if not check the freon charge, or thermostat, there will be a point where the aux. heat comes on when you turn it up, poss. only 4 degrees, is it a mercury stat or digital ? ... Ruud UAMB Air Conditioner
Ruud Heat Pump blows room temp on Heat and AC setting
A "Heat-Pump" is also known as a reverse cycle air conditioner, this means on heat the outdoor unit acts like the indoor section and vice versa. So in all probability you need to have it leak checked and recharged. ... Ruud UBHC Air Conditioner
Problems with a new Ruud heat pump "wiring"
Hello and welcome to FixYa!,It sounds to me like there may be a fault with the Furnace or that the Furnace is not compatible with the Heat Pump.It may also be a faulty Heat Pump.Hope This Helps, --P3NGYJ03 ... Ruud UBHC Air Conditioner
I have a ruud heat pump that tries to run aux heat
Hi, This sounds like it is cold enough, the ambient temperature outdoors and is bringing on the aux heat to help even at 1 degree. Nothing to be concerned about the energy you may use will be next to nothing.In the program of the stat as ... Ruud UBHC Air Conditioner
Ruud 300 thermostat in heat pump mode and I don't have the manual to get it out of that mode. It was working fine then switched to this mode. No more cold air. I live in Florida so I don't have a heat pump installed. I remember I had to switch to Electric mode but its a buncha codes. How do I switch it? Thanks
Hi,\015\012Here is the complete manual for your thermostat...\015\012\015\012Click here\015\012\015\012 ... Air Conditioners
Just had new ruud heat pump installed 5 days ago, it blows cold for the first few minutes and then warm but not warm enough, called installer he said thats the way heat pumps work and he will stop out when he can, can u shed some light on this problem. thanks
In most newer operations, the indoor fan motor will come on first before the actual heat comes on.\015\012However if you shut off the power and Remove usually\015\012the upper panel. Located on the inside on the right hand side there is i ... Ruud UBHC Air Conditioner
I have a RUUD 13pja42a01 heat pump. The main breaker in the house was turned off about a week ago. We have not tried to turn on the AC until today and the outside unit will not come on. The main breaker in the house is on as well as the heat pump breaker. I was looking for a reset button but cannot find one. Also in the box outside connected to the unit it does not appear that there is a breaker in there.
Check the small wires going outside to the contactor for 24 volts. If you have 24 volts then mayb ... Air Conditioners
Ruud heat pump outside unit not starting. Open and found contactor disengaged even though I have system on from inside. Low voltage wires come out of a circuit board checked for 24v, none. Then bypassed board by unplugging same yellow and brown wires plugged into the board and exiting but now I have 24v getting to contactor but it does not engage contactor. What could the problem be. I know a little a/c but these heat pumps are very complicated. Help please, I want to learn.
If you are getting the low voltage to the relay and it is not closing, then the relay may be either bad or stuck. Disconnect the 220v and see if the contacts can be manually closed. I always use a piece of wood or something non-conductive. If the ... Air Conditioners
My sister has a Ruud Achiever High efficency heat pump Model UPLA-049JAZ Serial #6408-M389910353 they just moved into this house in ND and have no information on this system..Over the winter it was very loud outside and they discovered alot of ice frozen on the fan blades and under but inside the unit. Where can they info for this unit and any suggestions on the freezup problem. Owning a heat pump is entirely new to them
There are 3 possiblites \012\0121. you have a bad defrost board or defrost sensor. \012\0122. Your low on Freon.\012\0123. Your coils and/or your Filter is dirty. ... Air Conditioners
Rudd upmc024jaz I have Ruud heat pump model UPMC 024JAZ, the air condition works great but the heat pump comes on runs for a minute or so and the compressor goes off. you hear a hissing sound from the compressor like pressure being released.
... Air Conditioners
Ruud heat pump model series pca high pressure cut out
... Air Conditioners
Ruud heat pump high pressure cut off problem
... Air Conditioners
I am thinking about purchasing a Ruud UANL -024JAZ Condencing unit, Ruud UPNL-024JAZ Heat Pump Condencing unit and Ruud UHSL - HM2417JA AC condenser for use in my house. Is Ruud a reliable/dependable product line?? Is Ruud's reputation for quality as good as Trane and Goodman units??
All brands have issues at some point. You should be satisfied with RUUD. ... Ruud UBHC Air Conditioner
RUUD 13 SEER HEAT PUMP MALFUNCTION 2009 MODEL
Unsure how long ago you purchased this unit, I can only respond to what I have read. I, as a homeowner, would not PAY a contractor until such contractor has properly INSTALLED and successfully TEST-OPERATED said unit/system in ALL MODES to the comp ... Air Conditioners
Ruud heat pump question
Does the air handler take a minute or two to start, this would be normal so that it doesn't blow cool air into the house before the unit is warmed up. If not could be the fan relay is weak and needs replacing. As far as the outside unit it sounds lik ... Ruud Air Conditioners
RUUD 14 seer heat pump makes loud squeeking noise after cycling.
Your problem is the TXV. I just had person with the same problem. Replace TXV no problem Rusty ... Ruud UAMB Air Conditioner
2 month long issue...RUUD Achiever 1.5 Ton 10 Seer Heat Pump
Rather than have him replace the control board first, ask him to remove all the freon and weigh it. He then can reuse the Freon that came out of your system put back in at the exact charge that the rating plate calls for. He will add a bit more to co ... Ruud Matching Split Air Conditioner
New Ruud 16 seer central air and heat pump - very noisy
A few things to check\015\0121) Is the unit mounted on metal brackets attatched to\015\012the house, is so I would probably put rubber pads\015\012between the unit and the brackets to absorb the\015\012vibration.\015\012 ... Ruud Matching Split Air Conditioner
Ruud 5-ton 10 SEER heat pump compressor turns off after 20 minut
You may have cottonwood on your compressor. Before you spend any money, do two things. Rinse off your compressor to clear any cottonwood, and check your filters, they may need to be replaced. Hope that helps! ... Air Conditioners
Ruud heat pump makes a clicking sound
The term H.P. is just a reverse flow a/c. do you have one big machine outside or do you have the h.p. outside with the "airhandler" inside. up in the attic, a closet,garage, etc?\015\012\015\012if the sound you hear is coming from the air ... Ruud UBHC Air Conditioner
Ruud achiever heat pump
If back-up heat comes on when a/c is turned on and then the back up heat turns off shortly after the a/c turns off, then the low voltage wiring is NOT correct. Your "R" terminal is basically your "hot" and your "C" terminal is basically your "neutra ... Ruud UBHC Air Conditioner
Ruud heat pump capacitor size
A hard start or turbo 2000 will not work if the run capacitor is bad. You will need to contact a ruud supply house or dealer with model and serial to find out the exact match. I have checked my sources and came up empty handed. You could try getti ... Air Conditioners
Ruud Achiever 10 heat pump - outside fan won't shut off
Definately get this checked out. Some thing has shorted just enough to let voltage "Feed back" and keep the fan running. Could be capacitor, wires rubbed through each other, etc. A reset is a safety that is used when there is an overcurrent or ove ... Ruud UBHC Air Conditioner
Ruud Achiever Heat Pump - Air Handler Thumps before Starting
... Air Conditioners