Having problems with your Air Conditioners ?
A/c hoping can get help few different things all revolving around the blasted a/c
first whenever the a/c kicks in every light in the house dims for the initial boot up then good doesn't kick anything off just common sense says when it dims that much to everything else hoping nothings wrong ain't the best thing secondly looking at the a coils on the a/c unit model # c30a 054u on what I believe in an Intertherm unit also looking to clean the thing in hopes of helping to reduce the bill the a/c un
The dimming of your lights at start up tell me two things, One is that the starting Amps may be a little high and drawing too much amperage. Have this checked by using an Amp meter. Secondly, look at your circuit breaker box. Does the Amp total on the right side of the box equal the left side. What I mean is that the Amp load of your box should be as close to equal as possible. If you have too many drawing Amps on one side, it puts strain on that side and will effect all breakers (loads) on that side. You can check this by investigating what circuits are on the same side of the box as your A/C unit and watch the lights associated to that same side and see if they dim when the unit starts. Also watch other lights associated to the opposite side and see if they dim. If they do, you have a compresser issue.\015\012\015\012To clean the coil you can purchase a coil cleaner at a local A/C repair shop and use a garden sprayer to apply. Rinse off the coil slowly and after you give it a chance to work. Too much water on the coil when rinsing will cause a flood in the bottom of the air handler and may not allow the drain to exacuate the water as quickly as designed. Rinse in moderation. Do this with all power off and the breaker locked in the off position.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
A/c hoping can get help few different things all revolving around the blasted a/c first whenever the a/c kicks in every light in the house dims for the initial boot up then good doesn't kick anything off just common sense says when it dims that much to everything else hoping nothings wrong ain't the best thing secondly looking at the a coils on the a/c unit model # c30a 054u on what I believe in an Intertherm unit also looking to clean the thing in hopes of helping to reduce the bill the a/c un
The dimming of your lights at start up tell me two things, One is that the starting Amps may be a little high and drawing too much amperage. Have this checked by using an Amp meter. Secondly, look at your circuit breaker box. Does the Amp total on th ... Air Conditioners
No Power Like everyone else the unit was working fine the 1st summer. Pulled it out again and nothing. It powered up for about 30 seconds then shut down. Now no power at all to the control panel. Is there a fuse link, or some kind of auto shut off I should be looking for? I can't say if it still blows hot and cold as I can't power up to find out.
Did you check the drain switch ?? this will shut them dowbn as well? ... Danby DPAC8399 Air Conditioner
Batteries on the control unit thing ran out, so I took the whole thing off the wall (not realising that the batteries can be replaced by pressing a button at the back of the unit to reveal the battery compartmnt), replacd the batteries and it looks like it works (display on, showing temperature etc), put the unit back on the wall and ... nothing, zip, no response. Help! Surely taking the unit off the wall wouldn't break it? It came off easily enough, and goes back into place just as easily.
Hi, check the wire connections to make sure the Red wire is good and tight. This is only low voltage, so don't worry about getting zapped. If all wires are tight. you may have blown the control fuse at the indoor unit. Go to it with a good light, pul ... Honeywell Air Conditioners
We have a Dometic Duo Therm airconditioner on our RV. The model number is 620515.331. When I climbed up on the step ladder to have a look at the roof of the coach, I noticed that encircling the unit, it looks like a kingsize bird's nest replete with twigs, grass, etc. Nothing seems to be alive in there, so we can only hope that all this stuff was sucked into it when the air was on. We have only used it a few times. We have no manual with the info from the RV dealer. Can we take the scr
Yes once you remove the screws the shroud should come right off. The cover is just that, the cover for the unit. You might think about putting some screening around the opening to keep this material out. ... Dometic Rooftop RV Air Conditioner
I have a Goodman CPLE42-1 split system. I had a power outage and my first floor unit would not cool anymore. The air handler/blower in the ceiling is working fine, but the fan outside is not turning on. When I went to look for an overload reset on it, I switched off the breaker on my second floor unit by accident, and now it is doing the same thing. Both fans on the outside will not turn on. Both thermostats will turn on the air handlers in the ceiling. Seems like I re-created the same exact pr
... Goodman CPLE24-1 Air Conditioner
My Split system Centrex CTAR60GW turns off about 10 minutes of cooling, the actual unit flashes on the timer button, have cleaned it replaced batteries and had 4 technicians out to have a look all of which says their appears nothing wrong with it. I am over paying call out fees for someone to tell me nothing is wrong when clearly there is as we are roasting in my house. I can turn the system on during the evening from about 10.00pm and it works fine throughout the night until morning when the ou
Dear friend. the timer problem is very common. Remove battery from remote and also remove power to unit. Again plug power on unit and start with remote and try to cancel the timer on and off. Press set.And also cool setting must be minimum 3 d ... Danby DPAC12031 Air Conditioner
I have a Fujitsu ASU9RMLQ (or 12RM or 18RM. That is what the manual states). The green timer light blinks twice every ten seconds on the indoor units in both rooms. The manual says to cancel the timer in timer mode. However, the lights continue to blink. I'm hoping this is the reason the outdoor unit is not operating. Any ideas? Thank you!
Yes somtime it hepense but if your outdoor unite is not working meant someproble with your elctric systems \015\012\015\012chack your line then only u come to know the problem ... Fujitsu Air Conditioners
Airco Indoor unit SC 12 ZKG Samsung After a while, 2 seconds to several hours the unit switch off. Lights on the unit green and yellow blink for several seconds. The switch off time is increasing shorter. Started with several hours now a days it only last a few seconds to switch off. In this country (Mozambique) is not sufficient kwowlegde to repair the unit. It was working for about 4 years. What can be wrong? Beste regards, Cees van Perlo - Electronic engineer [email protected]
... Samsung Air Conditioners
I purchased an Amcoraire split system unit for my 2 story garage. Licensced electrician did the wiring and licensed HVAC co. installed the 2 indoor units and outside unit. Outdoor unit is Model # AOM 243 HX 24000 BTU Indoor units are both Model #AWM123 HX, 12000 BTU each When I turn the unit on, it runs for about 60 seconds and then I get an error code on the inside wall unit that says P7. My manual says this has something to do with voltage. I had the power company come out and they show the
Since the manual says the error code has something to do with voltage it means the voltage is either too high or too low. And as the electric company says the voltage is within limits the the error is as a result of the voltage fluctuating. All you h ... Amcor Air Conditioners
I am reviewing my ac unit from condenser(outside) to evapoarator (inside). The inside evap is freezing-up,???I am blowing out evap (it looks clean)and cleaning blower and all air handling (they look oK). I have had service (SALES CALL) from big HVAC contactor ( says need new unit 12-14G ) says he will fill freon 2-3 lbs ($189 + 90 first lb, and $60 each additional lb) NOW after reading all your responder"s comments, I suspect the schrader valve is slightly leaking (I have had this happen on tire
I would suspect the unit was freezing up the whole time you were out if the ice is all the way out to the condenser and over the compressor as well as it being thick and solid. The shrader type valve could have finally leaked out enough and you can c ... Whirlwind FH-778 Air Conditioner
We have mitsubitshi mr slim air conditioners one of the units has what appears to be mold inside the unit. one repair man wnat s to take the unitis off and clean them out anotjer says he would spray chemicals into them but not take off the unit one says this condition is typical- the other syas it is not I don't know what is best
It is not always normal but it does happen and there is a chemical that can be spryed right into the coil and pan that is very affective not necessary to pull off the unit ... Air Conditioners
LED light blinks once when power applied. nothing happens after that. someone looked at it from an hvac company and ordered a board which looks nothing like what is oon unit. PN on board S1-33102956000. internet shows replacement board is 50A55843. It looks like it fits. should i send other one back and replace board with 50A50-843 and try it or should i trouble shoot further? what do i try?
Need make and model number of unit please. ... Air Conditioners
My air conditioning unit stop working (outside unit). When I turn the unit I notice a buzzz sound comming from the unit. I have pressed the reset button on the unit to see it that would help but nothing happend. I check to see if there was electricity with a voltemeter and the unit is getting current all the way to the capacitor. I turned the power off to the unit to check if the capacitor had a charge and it did. What other things should I be checking? Also, the fand do not turn on! model numbe
Hi, what is happening is, you have power to the outdoor unit. I am glad you have a volt meter. This system is a split unit,condenser outside and indoor unit. This is what you need to check, and what the buzzing is, and why the fan and compressor will ... Ruud UAMB Air Conditioner
My A/C outside will not run, inside a fan is blowing air (a little cooler than the 82 degrees it is in here, but not cold). Unlike all the other posts I've read, my unit outside is not making any noise. I makes a click when I turn it on at the termostat 1 time and then nothing. All this started yesterday sometime, after the remains of TS Fay left us. Help. I tried the breaker thing and resetting the 240v box thing outside at the unit. Help.
I am not an a/c expert but mine did this one time and it was the transformer I think it is called pull the panel off and look for wires burnt at connections also. BE sure you cut power off before doing this ... Carrier 38CKC042 Air Conditioner
My Goldstar Dehumidifier has stopped My Goldstar Dehumidifier has stopped working . I have opened it completely up and after cleaning it out, things look fine. For a little while before the shutdown it was making noise as it was starting up. Now nothing will happen on the LCD screen. When I plug it in I hear a beep like it wants to More My Goldstar Dehumidifier has stopped working . I have opened it completely up and after cleaning it out, things look fine. For a little while before the shut
Try the following tests.\015\012A.- First unplugged the rotary switch and plugged in the dehumidifier \015\012and it runs.\015\012B.- So figured that the rotary switch which is basically a \015\012potentiometer was failing. Took out your ... Air Conditioners
I installed a 2400 BTU Senville mini split ac unit about 6 months ago and until now, it worked great. Tonight I noticed my room getting hot and looked up at the wall unit and it was flashing "f5" I think? I turned it off and on and it seemed to return to normal with 65 degrees displayed yet when the room stayed hot, I went out and looked and the compressor was not working. I flipped the breaker and still nothing, went inside and turned it on and off again, still no compressor, no cooling. Thanks
... LG LS-K1830CL Cool Mini Split Air Conditioner
Have a Haier HWR05XCB air conditioner window unit that has been sitting in the garage for a few years. I cleaned it up for use in a room and plugged it in and nothing but Zeros on the digital display (00) only for about 1 second, then absolutely nothing, power button does not work. It does this every time I plug it in, I have tried several different outlets. No evidence of anything burned up or otherwise wrong from visual inspection. Is there a reset button somewhere on this unit?
... Haier Preference Plus HWR06XCA Air Conditioner
I have a ruud ac unit model # rcba 3765g. I removed the filter and look up at the coils and noticed that the dirt was caked on the them. What is the best way to clean them. It looks like it will take some kind of a solution to get it off. The unit is about five years old and the coils have never been cleaned. Thanks, Paul
Welcome to Fixya !Here\012 are some steps that you may follow. Take come caustic soda ,(put a table spoon in one glass water) that will be in powder form (caustic soda) , if you do not have this caustic soda , the ... Air Conditioners
Have a problem with my Intertherm air conditioner not coming on so I put a new thermostat on it. Nothing comes on fan nor heat nor air. I reset the breaker but still nothing and the unit model is a E1eb015ha? Anyone know if there is a reset button on the unit or where I can start looking to see if there is a problem.
Turn the thermostat off and check for 24vac between R and C on the thermostat. If there is no C then to G or W. If you don't have 24vac go the transformer and check for 24vac on the secondary. If it isn't there then check for 120vac on the transforme ... Intertherm P3RA-048K Air Conditioner
A/C outside unit will not run. Inside works, breakers are on and did not trip. No noise coming from outside unit, except for low buz when 1st turned on. After 10 seconds, nothing. Goodman # CPLJ36 - 1B. No idea how old. Have tried turning breaker switches off and on. Has been 24 hours, just tried again . . . nothing happens but that short buzzing sound, a low beep, and then silence.
Sounds like your contactor/relay on compressor defective, by the way it sounds the buzz is from the magnetic coil on the contactor but its not pulling the contacts in to start the compressor ... Air Conditioners
Furnace trouble Working on a Carrier sx from 1990, has three wire bi-metal pilot with spark and 100% lockout on the spark module. Homeowner says it only fails in cold o.d. temps (less than 35 degrees). Home owner finds unit off and silent, resets 120v and unit re-lights and runs. Don't know what parts have been replaced so far but it looks like a new spark mod. and the pilot was clean but I cleaned it again. Limit switch looks old but I think limit failure would cause the blower to run. Any idea
... Air Conditioners
The unit was blowing black/grey foam pieces on to the floor-pulled the cover & the only thing that looked obvious was a "filter" that sits horizontally in the unit..??? This is an older model-the fake wood look-The apartment was built in 1985. Thanks P.S.-do these require maint.?
Sounds like the filter is dry rotted!!! after a few years it is a good idea to replace the a/c filter,you can buy them at just about any department store and they are cut to fit!! ... Air Conditioners
We wanted to purchase a heater for our cottage. The one were looking at was Farenheat # 30263 4000 watts at Lowes. When reading the pamphlet inside the box it stated for best results it was better to leave it running all the time. We are at the cottage only a few months a year and didn't want it running all the time, so we decided this was probably not the best thing for us. The other thing that we realized was that eventhough it stated it had a thermostat we couldn't set a certain de
Hi Vicky,Don't be mislead...The electric heater that you saw at Lowe's is no different then any other...you can turn any electric heater off and then turn it on as you wish too....it will not hurt it... the only reason for that caution is ... Air Conditioners
Furnace shutdown have interthern heat/air unit , last spring it started shutting down and blowing out the pilot. had a serviceman out couldn't find anything wrong said the firebox looked ok but needed a new unit. later i found out if i leave the front cover off the furnace ran just fine . had two servicemen look at it & couldn't find anything wrong , big bucks for nothing , HELP! TB
If it runs with the front cover off.....it sounds like an air problem.Is this a 90% efficient unit?If so,it sounds like one of the plastic flue pipes is restricted. ... Air Conditioners
Working on a Carrier sx from 1990, has three wire bi-metal pilot with spark and 100% lockout on the spark module. Homeowner says it only fails in cold o.d. temps (less than 35 degrees). Home owner finds unit off and silent, resets 120v and unit re-lights and runs. Don't know what parts have been replaced so far but it looks like a new spark mod. and the pilot was clean but I cleaned it again. Limit switch looks old but I think limit failure would cause the blower to run. Any ideas?
Check the heater relay on the control board found in the blower part of this furnace. It's found in a steel enclosed box I'm having the same problem currently. I now have the blower running constantly set the thermostat to on not auto. until th ... Air Conditioners