Having problems with your Air Conditioners ?
Gas Valve is leaking
I am a Nordyne dealer and you can replace your gas valve with a generic valve of your choice. You can try and find a supply house in your area that sells them or you can visit www.myhvacparts.com to find one.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Dear Sirs Have purchased a air conditioning unit model 11-lg-251. The system is loosing its gas charge. it looks the system has an internal, leak do you know of any problems with the gas or liquid charge valves. Shuld I replace the valves, or do you have other solutions. Best regards Ori Afek [email protected]
Hello sir/mam \015\012 before replacing any part please check from where the gas is leaking if the leak is in the line soldering is requirede and if the leak is in the valve then replace the valve so please call the tech for ... Air Conditioners
Gas Valve is leaking
I am a Nordyne dealer and you can replace your gas valve with a generic valve of your choice. You can try and find a supply house in your area that sells them or you can visit www. ... Intertherm P3RA-048K Air Conditioner
A r410a central system requires a line dryer, this devise has an arrow pointing the direction of flow, which should be at the condensing unit, does it matter how far from the unit it should be placed. when installing a new r410a system, do you open the liquid line valve to pressure test / leak check the system with nitrogen? and also to attach the vacuum pump, keeping the suction line valve closed until the lines are at -500 microns and ready to open and release the stored factory r410a gas i
Hi,Okay... I hope I get all of the questions for you....First....no the filter can be anywhere in the system....but are you using s liquid line filter or a suction line filter....often you will use a liquid line filter and in that case th ... Air Conditioners
I have an amana dual fuel heat pump with LP gas furnace. the furnace will not light. the ignitor heats up, acts like it's not getting LP to the burner and i don't get 24 volts to the pressure switch just above the gas valve, or to the gas valve itself. i cut the power to the unit, removed pintle to the gas valve to ck for gas to the valve and it's o.k.,. what do i need to check next, i don't know how to get codes out of self diagnostic system and don't know if these codes would effect the furnac
... Amana Air Conditioners
Older Sunbeam Heat Force 85,000 Btu, LP salamander heater with a spark igniter, small sealed circuit board, asco red hat gas valve and temperature switch. The temp switch is an Elmwood L295 1/2" diam. surface mounted ceramic, 2-terminal sensor. The Asco valve is a Red Hat normally closed gas 110v, 10.1 watt valve. On/Off control is a toggle switch. The problem: I turn the unit on....fan starts, gas valve opens, spark igniter light flame....all good for 15-20 seconds. Then the gas valve shut
Hi,The problem is that whatever is sensing the flame is not telling the control that the flame is on...Not sure what you have on that unit, but I suspect that it is a photocell that sees the light and then tells the board that there is fl ... Air Conditioners
My a/c (24000btu) refrigerant gas leak after about 2 month always. There is no visible gas leak place to see. But always every two month after receiving no cool from a/c the repairman says all the gas in the system leaked, but always no traces of the leak. What should I do? How to find the leak? It leaks over the time gradually.
Is this a residential central air conditioner? ... LG Air Conditioners
I have a goodman furnace model gmpn 080-4 92% 1997 Gas vave would not open after igniter came on. the voltage was 15 prior to sequence and 26 upon time for gas valve to come on. I ran a jumper from trans to gas valve and it opened. I replaced board. it functions properly now, but I still have 15 volts at gas valve when it is not calling for it to open. Is this normal? If not what could cause this?
General rule is 24 volts to operate control valve. check common at valve to white at valve or out of board. 24 in call, less than 24 when off. sometime s these things back feed or give a false reading. voltage can read say 15 volts but under a load i ... Goodman Air Conditioners
I have a furnace and i just replaced a combonation hsi sensor and after i did the gas valve wants to open the second the hsi starts to glow but then two seconds later the gas valve opens and closes and opens and closes VERY DANGEROUS WHY IS THIS HAPPENING I have 28 Volts going to my gas valve and it is steady
Was this a direct replacement sensor os was ther rewiring possible short ... Air Conditioners
Furance I have 2 Ruud Achiever 90 Plus gas furnaces. Units were installed in 2004. One unit flames out after ignition and just prior to the fan kicking in. Confirmed gas valve is functional by switching out valves. Check all wire connections. Could it be the remote sensor or another 24 volt sensor at the IFC that is locking out the gas valve?
There should be a flame rod that senses the flame , if not will shut off gas valve. It is a stainless steel rod that is in the flame path and wires into the panel ground. You might try to clean it with some steel wool or fine paper. Sometimes they wi ... Ruud UAKA030 Air Conditioner
I have ventless natural gas heater , u can lit the pilot , but when u let up off the button the pilot goes out . have replaced thermocouple the same problem pilot will not stay lit. have also used air compresser blew it out ,stillwill not work is there adjustment screw on the gas valve or reset button on the gas valve .
When you light the pilot, hold the button in about 1 minute to satisfy the thermocouple. Once the thermocouple is hot and satisfied, turn the gas to "ON". You may have to extend the time a bit, but 1 minute is usually enough.Best regard ... Air Conditioners
Turn Thermostat to call for heat (here click)from the t-stat calling. I do not here the multiple click (ignitor)and then the flow of gas. I have a Honeywell VR8204M electronic gas valve. I have votage coming from the control board "PV" to my electronic valve. My question is do I have to change the entire electronic valve or should check some other things first.
That particular intermittent pilot gas valve uses one of three ignition control modules; S86F, S8600F, and S8610. Check the pilot assembly and look at the flame, could be a weak flame, dirty or clogged, if its not lit or weak, you&rsquo ... Honeywell Air Conditioners
Intertherm gas furnace 80 % mod# MMHA-070ABHR-05 will not open gas valve and light <changed gas valve <control board<ignitor all three limits and still not working I have been in the hvac buisness for 10 years but cant solve this one ,the board is flashing a 3 code < i have called a fellow tech who had the same problem on the exact same model last year and he spent 10 hrs trying to repair this unit but was unsuccesfull also<i can make this furnace burn by wiring 24 volts direct t
... Intertherm Air Conditioners
I have a dayton gas furnace aand bought the kit to change it to lp gas. Ater installing the parts it does not work. The pilot is to big and i have adjusted the control all the way down. And thge valve wont open and let the lp gas to the burners. I replaced the valve and the thermostat and the thermocouple. Also am trying to use a propane bottle off my grill. is this the problem? I didnt want to spend the money for a large tank until I knew it worked.
Hi, Let me get this straight, you converted the original valve to l.p by replacing the spring and other small parts in the valve orfice ect. Then you had the problems. So, you replaced the valve, thermostat and thermocouple after that? If I am corre ... Air Conditioners
I have a Marco gas fireplace model# 794019C. It is the millivolt pilot generator type. I first changed the thermopile and cleaned the spark ignitor to get it to light. I have checked continuity and everything checks out. Damper switch opens and closes, burner wall switch is good. When I jump the the redundant gas valve with jumper wire from one of the three terminals it does turn the burner on. Some of the time it is hard to keep pilot light lit, it will trip gas valve when you move from pilot t
Mike, I suspect that the problem you're having is not related to the new Thermoplie (Pilot Generator) you installed. Its with the Thermocouple. The clue was "Some of the time its hard to keep the pilot light lit". The Thermopile controls the opening ... Air Conditioners
Dura-Glo Centurion Model 48 gas fireplace gas valve not letting pilot stay on; has new Tpile, which is activating valve (I can hear click internally when I hook up leads from hot Tpile. Unit wasn't used for quite a while and was found in "pilot" position but not lit. upon re-lighting (long manual hold time) started working properly. We thought maybe intermittent wind blowout, but then Tcouple quit making juice. Replaced, but now just a click from inside valve. I haven't found any tags on the va
Ed, when you installed the new Thermocouple did you finer tighten and just 1/4 turn more with a wrench? Or did you tighten it more than that? If you did over tighten it, the Thermocouple probably locked up the control valve. Unscrew it, give it a co ... Air Conditioners
Lost power, gas from the gas valve was still flowing into the heat exchanger even tho the piiolet was not lit..... should I replace the thermo coupling or the gas valve or both
Sounds like the valve stuck open. I'd do both just cause you are there. The thermocouple is not the much of an additional expense. No gas should ever flow with the power off. ... Air Conditioners
Water Leak from the hole where drain valve is attached
I have jw402na john wood water heater which is leaking from top cold and hot outlet..how to repir this leak ... Air Conditioners
De Dietrich 230 eco 170 hot water boiler fault. error code 14 (no flame),gas present at inlet to multiblock valve,1st stage valve opens but no gas flow.I have tested and checked pcu board,solinoid coils,wiring looms,restored factory settings on Diamatic m3 control panel,etc.at my wits end ,any thoughts?
... Air Conditioners
I have a Burnham series 2 gas boiler with honeywell controls. The taco zone valve control calls for heat or hot water, the boiler attemps to fire but goes to retry mode. This continues until I recycle power and it fires. My plumber replaced the gas valve, no luck.
Hello. The culprit is most likely the spark electrode lead. Once the pilot lights it rectifies the current telling the pcb [printed circuit board] the pilot is on it is ok to light the main burner. Begin by replacing the electrode lead. If it is ... Air Conditioners
My central heater is not blowing hot air, I am having to turn the thermostat on and off. I have the thermostat to 70, and the heater will blow hot air and then it will just circulate the air in the house, therefore bringing the temperature down. I looked at the unit and noticed that when the thermocople (heating element) goes red, the gas valve makes clicking and the flames come and then go out very fast. I noticed lots of clicking in coming from the gas valve. help please
Hi!!! relax your flame sensor is bad change and you will be fine..If it turns off and on change your flame sensor ... Air Conditioners
I have a Raypak pool heater with a invensys gas valve, the burner is not kicking in, pilot light is lit and stays lit, I jumper the complete switch circuit and still does not kick in. this is a millivolt system, do I have power? is the gas valve repairable? thanks Mike
Usually not the gas valve unless line voltage was applied to it. Millivolt systems are very touchy about connections. First check the output of the millivolt generator (thermopile) the wires for this usually go straight to the gas valve they shoul ... Air Conditioners
I have a 1985 Bryant central air Furnace model 395BAW048095 with a White Rogers 36E gas valve. The flue is metal and there is a fan within the furnace to create a vacume at the base of the flue pipe conection that turns on when a call for heat comes from the thermostat at startup to ignition. The spark fires but no gas is released by the valve for the pilot to lite. Added information: The blower fan is set to continually run, I replaced the pressure switch (306621) and the limit switch (HH12ZB18
... Air Conditioners
Just installed new Goodman 95% updraft furnace with 3" supply and vent lines going out through wall. Gas valve won't open. Circulation blower runs in manual on, A/C system runs fine. I have used an ohmmeter and voltmeter to do checks. The entire series of safety switches are closed. When the small blower is running, both pressure switches close. The igniter comes on but there is no voltage to the gas valve. Just after the igniter goes off, I hear a relay click, the circulation blower seems
Make sure you have bled your gas lines. If any air is in the lines, it will cause the unit to do exactly what yours is doing. The relay "click" you hear is the gas valve opening, but if there is no gas, it will not ignite. This is common for a new in ... Goodman Air Conditioners
I have a 2 year old Goodman GDS80703ANA furnace that has always had a problem starting. Sometimes it starts on the first attempt but other times it takes 2 or 3 attempts. This is what I see happening: The Induced Draft Blower starts and runs- the Igniter will glow for a few seconds and just as the igniter starts to stop glowing I hear the Gas Valve click and open but it is too late. On the next attempt or so, the Gas Valve will open sooner and burner will ignite. My question is: Is the Integrate
The board controls the timing ... Air Conditioners
Our whirlpool water heater is not heating. My husband replaced the thermocoupler and it still doesn't work. We have had it for 8-9 months. Whirlpool is sending a new gas valve. We are reading that this will continue to happen even with the new parts. Is there a universal gas valve that we could replace it with that will work or should we consider just purchasing a different hot water heater? The model number is BFG1F4034T3NOV.
... Whirlpool Air Conditioners