Having problems with your Air Conditioners ?
Low cool air
Because the model numbers are based on the country in which you bought the unit, you will have to do the research yourself on the error code for your unit. Once you find out what the error code is you can determine if low refrigerant caused the problem. Here is the contact info website to download your manual.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Sharp Air Conditioner AC09RLCSYS isnt cooling properly. Very moderate to low cold air from unit. At one point small bits of ice came out of indoor unit when on auto cool. Unit was switched off immediately and then turned back on after a few minutes with no additional problems, however still is not cooling properly. Unit is only eight months old. First used for cooling with no problems and great cold air, then for heating during winter. Now back to cooling and not getting the cold air like p
Unit may be freezing up if blowing ice crystals. Let thaw 24hrs try again. Make sure condensation drain line is cleaned out. ... Air Conditioners
My low cool air works, but when I put it on high cool, it does not blow air. The low fan works but when I put it on high fan, nothing happens.
Most likely the control switch is bad or burnt wire terminal ... Carrier Air Conditioners
MY frigidaire Air Conditioner model number: FAC107P1A2 has suddenly stopped blowing cool air. Check Filter light comes on but filter clean. Press Check Filter light button and blows out cool air for about a minute then blows hot air. Bought new at Lowes. Never had problem before with this air conditioner for 6 years! Please help burning up!
A few basic principles for air conditioner troubleshooting. For both central home air conditioner or window air conditioner,\015\012 the first thing to check is whether the unit is getting proper power. \015\012If the unit ... Frigidaire FAC107P1A Wall/Window Air Conditioner
Not cooling HQ2082KH air conditioner purchased 5-20-98. Used only in summer months. Yesterday started not cooling. No ice buildup, filter has been cleaned. When increasing the cooling number we use to feel it kick in. Now it is not doing it. Air coming in is not cold but cool but very low cool.
It sounds to me like u have a gas leak.you shouldent run the a/c until it gets fixed reason being that the cold suction gas is used to cool the compressor windings.if u continue to to run it you may end up in more expenses:-) ... Quasar HQ2082UH Air Conditioner
I have a 1988 Prowler TT with a Coleman TSR Mach3. I've installed a new blower motor.The fan side works fine on high and low but when i move the selector to High Cool the compressor does not turn on..however when i move the selector to Low Cool the compressor turns on and it cools for a few seconds then locks up..now fan no cool air. Any ideas?? Is there a way to change/add oil to these units? Thanks, Hot in Alabama
... Coleman Mach 15 Air Conditioner
This is a heating and cooling through the wall heat pump. It works normally when heating is selected - the heat pump runs and both speeds of the fan blow warm air. But nothing runs when cooling is selected. In other words the unit works normally when "High Heat" or "Low Heat" is selected but nothing runs when "High Cool", "Low Cool" or "Fan Only" is selected. The position of the Fan Cycle Switch has no effect - behavior of the unit is the same in both positions of the Fan Cycle Switch.
You have a bad board or bad switch. I would say board. You can have service tech check this out. There is only so far you can go without knowledge of Controls ad electricity. Russ ... Air Conditioners
1994 corolla-I charged the air cond., and it was cooling fine. After about a mo., it was not cooling very good. I assumed it had a small leak. I put my guages on it and the low pressure was running 15 to 20. The high side was reading about 150.I put a can of stopleak and detector in it. Then I put a can of freon in it. While I was putting the freon in it the pressure started to drop on both the low side and high side. Now the low side pressure is running about 15 and the high side is running 0.W
Hi\015\012\015\012\015\012Thanks for using FixYa. This has happened because of the low side pressure on your AC pump isn't kicking on, because when the pump is off, the pressures equal out and the low side shows a high ... Air Conditioners
When calling for cold air, the fan in the cooling unit hums, but does not spin. With a nudge, the fan does spin. Looks to be smooth and normal speed. However ambient outside air 80 degrees. the air through the register is 72 degrees. Is there a switch that will not allow the fan to start on its own if the coolant is too low? Do I have two problems, fan starting AND insufficient cooling? Unit worked well the last two days.
Sounds like start capacator possibly bad ... Air Conditioners
I am trouble shooting a Bryant Hi-bred system that uses an air cooled heat pump with high efficiency gas furnace for backup and low ambient operation. How does the system decide whether to use the air cooled heat pump or the gas fired high efficiency furnace. It appears to be outdoor air temperature related, but I can't find the setpoint for it. The main zone Bryant thermostat appears to control the system, but it doesn't always bring the backup heat if the heat pump doesn't function.
If you are using honeywell vision pro 8000 t-stat you need an outdoor sensor program on t-stat would have to look up ... Bryant Air Conditioners
I have a Friedrich 13,500 BTU WallMaster. The air conditioner stops generating cold air and seems to use the fan only on a regular basis. The front panel shows that the unit is still in cooling mode but the the unit just blows out warm air no matter how low I set the temperature. Then out of nowhere the unit will start cooling again. I know the problem is not the filter. Does anyone have any ideas? Thank you.
I'm having the same issu!!! It's horrible! ... Friedrich WallMaster WS07A10D Air Conditioner
Hi, Yesterday I noticed that my central air had low air flow and wasn't cooling the house, so the A/C was running all day. Just had an HAVC guy come in a filled and saw I was about 3LB low on Freon, he said I have a freon leak and wants to replace the indoor coil, which costs about $500+labor. In the 5 years I've been living here, I've never had the freon refilled before. Does it make sense that I would need to get the indoor coil replaced?
Hi\015\012\015\012It is always recommended to contact a repair tech. in case of Air Conditioners. I believe its been 5years and during this time you did not spend anything towards your central a/c. If you want you can also compare his cha ... Carrier Air Conditioners
I have a 1993 yellowstone camper with a coleman wall thermostat. on the bottom of it- it has a heat/cool switch on one side and the other side has a low-high-fan switch. when we run it on low or high it gets cool but the fan never shuts off.if we put it on fan it shuts off with the compressor but it doesn't blow cool air. any advise?
Thank you so very much for your answer! I'm glad I came to this website before I began a new project. I was about to re-wire my unit based on my ex-husbands advice!!!! ... Coleman Air Conditioners
This season we bought 3 Sharp CV-2P10SC portable air conditioners for home use. We have used the 2009 and 2010 versions of this unit previously and have been very happy with them. Not so with the 2011 models. Their cooling capacity is very disappointing. They cycle in an approximate 2 minutes on / 2 minutes off pattern. This is operating in an 85F ambient medium humidity conditions. When "on" the airflow is low and the air is not cool. When the unit is turned to "maximum" it shuts itself off! Th
... Air Conditioners
Will not blow cold air - low intermittent buzzing noise on cooling mode. Exhaust air cool.
Clean coils front and back....clean drain oil fan motor...take cover off relay...clean plugs and pins( from oxide)...if it starts hard get a hard start kit ... Air Conditioners
Both circuit board lights blink at the same time when unit turns on. Air pressure out of vents is low. Air is cool but not cooling house down.
Your filters might be plugged. if you just changed or cleand the filters and they were plugged the evaporator coil might be dirty not allowing the proper amount of air flow. The evaporator is usualy lokated right above or below the furnace in a coil ... Ruud UBHC Air Conditioner
Outside air temp around 100 unit wasnt cooling good noticed evap coils dirty cleaned them cooled alittle better checked low side showed 90 lbs had friend reclaim to get it to 70 lbs 30 minutes later it showed 50 lbs had friend put refrigerant back to 70lbs. cools good at night but during heat of day will only cool to about 80 degrees inside. unit 5 years old never had this problem before
90 psi suction too high possible bad valves or non condensablies in the system (AIR) what is the head pressure and what type of freon r-22 410-A? your unit is never shutting off watch out for that electric bill. and did you take apart the condenser a ... Air Conditioners
GSH13 Goodman heat pump split system is running a long time in cooling mode and will not cool below 74 degrees. A lot of condensation generated. The low side pressures 78 to 81 and high side pressures are 180 to 200 psi. Energized and deenergized the reversing valve several times.Pumped down the sytem (pumped down well) and checked the flowrater for any type of obstruction. Have a sight glass on the system - will get clear then bubble up. System is in the second cooling season with clean air fil
Check sub cooling and super heat. the New ac units are very critical to charge. There is a charging chart on the inside of the cover to the unit outside. Check temp difference across coil. Should be 18 to 22 degress. If you have an ampmeter. Check th ... Goodman CLQ36AR49 Air Conditioner
Wall A/C only SPORADICALLY blowing cold air. Turn it off and back on, you can feel it's cold, but only if you're 5 inches from it. After a couple of minutes, fan is only blowing warm air again. Vacuumed front of A/C, still doing the same thing. Filter is clean. It is over 100 degrees outside with very low humidity the last few days.(Los Angeles) ; since it's a wall a/c, of course 1/2 of it is outside in the heat. As I noted, if you put your hand right up against the front, you can feel cool air
If it blows be not with force like it used to it can be fan motor capacitor not boosting fan speed. but if speed is not the issuse. remove and clean both coils water hose ... Air Conditioners
Air conditioner is not cooling. The fan is running. When I turn the thermostat past 7, the unit shuts down. Any ideas? Low on Freon?
Sounds like a leak to me - if you have a set of guages available (know anyone working in the refrigeration field???) you could tell this for certain. Otherwise, try running it when it cools down outside and see what happens. Take a stick ... Air Conditioners
Low cool air
Because the model numbers are based on the country in which you bought the unit, you will have to do the research yourself on the error code for your unit. Once you find out what the error code is you can determine if low refrigerant caused the prob ... AmcorAire UCHW-H12AF2 Split System Air Conditioner
I changed the batteries and now the house will not cool down. The lowest i can get the house cooled to is 76 degrees, and that is if i turn the thermostat down as low as it will go. The air coming out of the vents isn't really cold.
Check the filters. Clean or replace them. If you are refering to the batteries in the remote, look for a reset button or hole and stick a paper clip in it. You will have to reset your clock. ... Honeywell Air Conditioners
Hello. My General airco (in Cyprus) works 10% normaly. 90% it start and stops after 10 seconds the it gives low air. But sometimes, today the first time, it works normaly, but when I switch it of and start after some hours again 10 seconds cold air. 10 seconds of. Remote control: Cool Fan control High Thermostat 16.
Hello\015\012\015\012If it was a general AC it must be running on a vapor - compression cycle, it must be the refrigerant (freon) that might have leaked and ran low causing the compressor to pump less refrigerant and is working on a low p ... General Air Conditioners
Have a coleman mach unit that never cools correctly. If you run on low with thermostat halfway down it will keep running. If you run it on high, it acts like the coil is freezing up and barely blows air. I assume it is low on charge. Is there no way to add a charge? We have had our rv only 2 years and they replaced the unit once already.
It may also be an obstruction in the ducting. When the forced air is restricted somewhere, it will freeze the coils, and compressor shuts down, until frost is gone, then starts back up and will repeat that all day. I'm thinking that the restriction d ... Dometic Rooftop RV Air Conditioner
Hi everybody i want some help , iam a technision in air conditions ,i was fix a central ac carrier and i found that everything works good the compressor and the high pressure fan and indoor fan ,but the problem was there is no cooling and the low pressure pipes werent cool and no drop of water on it , what i do ??????????
If the compressor is running - the suction pressure should be 65-75 psi - if it is very low - not enough freon - if it is very high - the compressor valves could be damaged - both will cause this ... Air Conditioners
All of a sudden the air conditioner no longer cools, with hif=gh or low thermostat settings. The fan for "Fan" and "Cool" settings works normally
Sounds like the outdoor unit is not working check breaker and then the capacitor ... Maytag M3X05F2B Air Conditioner