Having problems with your Air Conditioners ?
Samsung AW1003M Air Conditioner how to clean Fan inside??
Hello! there well, there are two fan coupled together on a/c the condenser fan and blower fan,if this is split type the fan and blower are separated.the procedure is the same way.doing this release lock off and take off front cover then pull out ac unit assembly,after pull out,open terminal control box disconnected all wiring connected on compressor motor and fan motor, loosen all stud bolt on compressor blower fan case.this well exposed fan and blower w/ the motor.cover the motor of plastic sheet then, pressurize water wiil use to clean blower fan observed the motor not to wet by water if this wet don't try to run let it dry off or else this wii burn out so take all necessary precaution, beside mosly cleaning procedure includes the fin tube of condenser and evaporator there are foriegn particles and moisture emerged in evaporator mostly that why insufficient cooling effect on condenser heat rejection also affected if dirty fin tube emerged,.theres is lye detergent use and mix to water pour this to evaporator and condenser fin tube wait for 15 to 30 min soaking to rinse dirt will come out to fin.observed not to distorted fin of tube on eveaporator and condenser.,then pressurise this by water again if cleaning was done dry it off until all dirt disappear.if finishe put back all casing of compressor,evaporator and condenser, then connect all electrical control connection on circuit board, double check connection just put back what ever disconnected parts dont try to alter specially electrical control connection on circuit board.this is a hard task and risky if yout not qualified to handle this job bring it or call a service technician.have a nice and cool day regards and thank's.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Samsung AW1003M Air Conditioner how to clean Fan inside??
Hello! there well, there are two fan coupled together on a/c the condenser fan and blower fan,if this is split type the fan and blower are separated.the procedure is the same way.doing this release lock off and take off front cover then pull out ac u ... Samsung AW1003M Air Conditioner
Hi, I have a samsung aqv18ja series split type air conditioner (cooling and heating) wall unit. the unit was install in 02/12/2009. By "one hour heating and air conditioning". In this short time service the outside compressor has been replace, the system has check and recheck,for cooling leak. the inside unit fan motor has been change. but the problem still exists. The inside unit fan continues to run when the unit is "off" and with the remote off.
Simple, check in your remote. There is an option button "Blow". Just press it. Your unit gets completely off. Please write back if helpful? ... Samsung Air Conditioners
Daikin split cycle air conditioner FTXD50J heaps of water coming out of interior unit 1. Do I have to unblock drain hole on the interior unit or the external unit. Also dont have any compressed air 2. Also very whistley almost drowns out the TV can I lubricate the bearings? If so what do I lubricate it with and how do I get to them. 3. roller fan on inside unit is all gunked up almost solid with dust Can this be taken out and cleaned some how or how do I get it back to a new condition? many than
You will need to find where the unit is clogged and try and run something up through to snake it out. In regards to the whistling noise, this is usually caused when there is debris that has collected and the air is trying to be sucked through a prev ... Air Conditioners
My dometic RV rooftop air conditioner is leaking on the inside of the camper even after I cleaned the water condensation drain on top of the roof. What could be causing this? The fan is blowing the water into the filter area in the camper, thus it drips onto the floor.
Remove all covers and look down with them removed and see if the coil drain pan has a stopped up exit where the water drains out and into the rear of the AC unit. If the unit is off level it could cause a draining problem too. ... Dometic Rooftop RV Air Conditioner
Bryant air conditioner - outside unit will not run - before it quit running, air temperature in house rose from 65 degrees to 75 degrees. Inside fan continued to blow - air smelled like a car air conditioner that ran out of Freon. Bought Freon - need to know where to add it. The heat pump model # BF-163S bi directional but also coming from unit is another line that runs same direction with same type of valves. Air conditioner model # 697CN030 - B
... Air Conditioners
AC Out. Two year old house. Goodman A/C, two units one for upstairs. Cleaned coils of both outside unit, replaced filters, re-set breakers. Upstairs is cooling. Downstairs unit is running outside, not circulating air inside (inside temp 87). Vents inside are cool to touch, no air. Outside unit fan is pulling, but air exhaust is cool. Compressor ? Should air be circulating even if compressor not functioning. Is there anything in attic exchange that would affect downstairs circulation. Thanks.
Assuming that the 2 systems are isolated, that there isn't any cross over between the systems...It is normal for an air conditioner system, from window unit to central, to be able to circulate the air, even if not cooling. This is known ... Air Conditioners
Hello, We bought a Perry Home in Georgetown TX last March and it is still under its two year warranty. Our air conditioner stopped cooling today. It has been working well for over 1 year. We came home from work and the temperature is 86F inside and climbing. My wife left the house at noon and the temp was 76F (where we keep the thermostat in the summer). The Air conditioner outside unit's fan is operating and no noise. The inside blower is running normal - no problem. The model number on the o
You have a 10 year warranty on your AC. Call a Goodman rep and have it serviced. It will probably be a bad compressor capacitor. Bad wire or no refrigerant. ... Goodman Air Conditioners
The inside of my air conditioner is full of mildew. When turned on, it spits out small pieces of black mildew. The odor is very obvious. I cleaned the louvers (as much as I could reach) with a Q Tip and sprayed the inside with Tilex Mold and Mildew Remover. That helped, but the mildew continues to build. The air conditioner is in my bedroom and since I have asthma, this is not good. I have a Fedders in my living room and have never had this problem with it. The Haier is only two years ol
Ruth this happens alot ive answered alot of questions so im going to make it short please give me a vote and rating the unit needs to be pulled out and taken out side sprayed really well with cleaner homedepot and lowes sells coil cleaner in their a/ ... Haier Air Conditioners
I have three mr slim inside units...live in a very clean place, non-smoker, no pets, brand new renovation....problem is that the fans are constantly getting dirty. less than a month ago i had all three units taken down, thoroughly cleaned, drain hoses cleaned, etc. Put them back up and now they are accumulating what appears to be an abnormal amount of gunk on the fan blades. the filters are clean, the coils are clean, and the air intakes at the top of the unit are clean as well. anyone have any
Very strange indeed! The ffault is on anyway and there is a dirt that comes on to stick to the fan. So the logic is that the fan is bringing up the dust to the fan either from the inside of the unit or from the outside. if you are spot sure that ther ... Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Domestic "Quick Cool" RV air conditioner Fans blow good, air filter clean, went up top and with A air compresser and blew air threw both sides of the coiled Radiators. All clean up there. Capasitors are good and compresser. Runs good. But still no cold air. Do see one tiny line frosting up. Idea's
... Dometic Rooftop RV Air Conditioner
Coleman RV Rooftop Air Conditioner - cage fan making a noise like it is hitting on something as it goes around. The motor works as it should, low and high fan and cool, the air is cold. The only thing that is a problem is the sound. We have already removed the top from the roof and the bottom cover from inside so we can see the cage fan, but cannot see what it could be hitting. Any ideas?
Hi,\012Those squirrel cage fans have a habit of coming apart, or getting dirt in them and going out of balance...then they wobble and hit the sides of the fan housing...\012Make sure the fan is clean and also move it around a bit to make ... Dometic Rooftop RV Air Conditioner
When I try to run the air conditioner it sounds like it's trying to cut on and then it stops. It tries this over and over. One time I heard a very loud pop come from inside of it while it was trying to cut the air conditioner on. I have left it on fan since. Any idea what this issue is....?
... Royal Sovereign ARP-3012 Air Conditioner
Lennox air conditioner. Outside unit fan stopped spinning. Air coming out inside the home. Unit is on and operating. Fan just stopped. What is wrong and what should i do?
Hello, this sounds like a bad capacitor or bad fan motor. Replace the capacitor, if replacimg the capacitor does not work you have a bad fan motor. Capacitor is usually about 10 bucks where a motor is about 200. So try repacing the cap first. ... Air Conditioners
Hi Expert, my reverse cycle aircon is Samsung model name=AQY09NSBN, only fan is working on the outside and inside unit at the moment, no heat air or cool air coming out of the inside unit, even tried with different temperature setting. Everything was fine till my gutter downspout was blocked and the switchbox outside near the unit was flooded and the aircon was on and off by itself every three seconds, so I turned the aircon off from the main switch outside. I got an electrician to replace the
Hi, and no your warranty is not void due to a flooded disconnect box, this is a lie!! If both fans are running, and you have no heat or cooling, the compressor is not running. This is a heat-pump with a reversing valve. The indoor unit has a control ... Air Conditioners
Borg warner Is the old round York Borg/Warner thermostat incompatable with a Honeywell? I just replaced my old round mercy switch thermostat with a Honeywell RTHL111 thermostat. The air conditioner service man says it is hooked up right, but the fan on the unit will not run on auto (it must be in the on position on the thermostat [thus the fan runs all the time]). He also replaced a relay switch inside the unit. We are using air conditioning only on this unit. Red to R (strapped to Rc), gree
... Air Conditioners
Trane XL 1400 air conditioner unit. the Fan on the unit will not stay running but motor continues to hum. Inside fan blowing warm air into the house
... Air Conditioners
Goldstar r0501m I have a GoldStar R0501M Air Conditioner mounted in a window. The issue that I'm having is after a few days of (non-continuous) use, enough water builds up inside the machine that the fan starts audibly splashing through it. I cannot see any sort of drainage hole on the outward-facing half of the machine, and have been resorting to tilting the whole air conditioner to drain the water through the power cable hole. How is it meant to be drained?
... Air Conditioners
Fan inside air conditioner won't turn on
Mine was the calculator box was bad cost me about 15 bucks for another, because i had the same problem, my air would come on but the fan wouldn't turn. Or their is a wire loose, or dirt inside of it. hope this helps.. and i do know if you run it and ... Air Conditioners
My air conditioner delivers cold air only in spurts. It then goes into fan mode for a few minutes, then to cold air in a few more minutes. It is over 100 degrees outside and the inside of the house is 85 or so. I have the temperature set at 74 degrees. Why does the cold air not pump out consistantly?
Hi,The\012 unit is probably low on freon and so it is running too cold....this \012trips the freeze stat and shuts down the compressor till it warms up The unit will \012need to be recharged or replaced...\012Here is a t ... Fedders AED24E7F Wall/Window Air Conditioner
I have a split system air conditioner. the inside fan turns on fine but the out door will not. i pushed the contactor in (located at the outdoor fan)that seems to turn on the fan. i measured the voltage with multimeter across the contact 24 volt side and got low voltage reading. then i disconnected the wires to the 24 volt side of the contactor and measured the wires, the wires read 24-27 volts. i dont know why when i connect it the readings are low. i even got a new contactor and still the same
Contactor working means fan might be bad can you feel any resistance from fan or bad capacitor. ... LG LSC091PMA Split System Air Conditioner
My Friedrich Quiet Master window Air conditioner blows cold air for a couple minutes then switches to warm air, almost like it switches to fan mode. We also are getting water blowing in. We cleaned it, this helped a little. Could our cooling problem be with the thermostat?
Air conditioner may be too small for the room.If the air conditioner is put in too large of a room the air compressor will freeze. If you take off the filter you will see ice inside. The best thing to do is let the AC thaw out unplugged and put ... Air Conditioners
B & D company air conditioner(model# 566DJ024-C) makes buzzing noise. I just bought a house and when I turned on the air...the unit outside makes a buzzing noise. The fans seems to work and cooler air is coming out of the vents(only ran it for a few min,didn't want further damage). I had the home inspected and the inspector said that the inside breaker is 30amps and the actual max for this particular unit is 25 amps. I don't know if that is the problem or something else...just thought I'd mentio
The circuit breakers Ampere rating has nothing to do with the buzzing noise. If you use a lesser Ampere Circuit Breaker it will trip every time the Air Con: starts, and if you use a very high Ampere Circuit Breaker it won't trip and give you the need ... Air Conditioners
My lg 15000 er air conditioner is blowing hot air i could hear compressor starting for five minutez of cooling the n shuts off and hot air again i have cleen filtered and cleaned coils inside part
Hi,The unit is probably low on freon and so it is running too cold....this trips the freeze stat and shuts down the compressor till it warms up and you reset it by turning it off and then on again...The unit will need to be recharge or re ... LG BG8000ER Air Conditioner
Our uni-aire reverse cycle air conditioner (model HAN-L6) is not as cold and the fan speed is not as high as it used to be. The unit is 2 years old. The internal air filter is clean. Could it need re gassing?
The fan speed could have a lot to do with the problem you are having. If the speed isn't right the a/c could ice up or not supply the proper air temp. 2 things could be happening here 1st the capacitor for the fan could be going out causing the fan ... Air Conditioners
Recently bought samsung multi split 3 rm air conditioner. 2 of the room air con working fine but the 3rd room fan coil seems to be blowing only cool air not like the other 'aircon' feel coolness. Got the technician to top up gas but same problem persist. Help!
Doesnt sound like a gas problem. theres a vavle they opens and closes inside the unit that might be playing up either the vavle or the indoor pc board. did it ever cool ? might also be the vavle on the outside unit were not open with the alan keys so ... Air Conditioners