Having problems with your Air Conditioners ?
New furnace, goodman and reinstalling squirrel cage... unsure where to put red wire running from squirrel cage
Follow your schematic on the new unit. It will tell you where the wire goes. Some of the "extra" wires are connected to the main board close to where the "used" wires are and they are labled "spare". Find the blower motor on the schematic and trace out where this wire will go.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
New furnace, goodman and reinstalling squirrel cage... unsure where to put red wire running from squirrel cage
Follow your schematic on the new unit. It will tell you where the wire goes. Some of the "extra" wires are connected to the main board close to where the "used" wires are and they are labled "spare". Find the blower motor on the schematic and trac ... Goodman CLQ36AR49 Air Conditioner
Replacing the thermostat, took the old one off without marking the wires. Hooked it up by color and we get the furnace when we put it on cool. wires are green, red, yellow & blue (ground wire)on the wall. The new thermostat wires are red, yellow & green. Can you tell me which wires go where correctly?
The normal wiring for stats is white=w=heat,red=r=24volts,green=g=fan,blue=c=common,yellow=y=cooling.\015\012see what ties into your furnace board and match the terminals. ... Honeywell Air Conditioners
Self contained a/c unit i put new blower motor in it about a year ago and never used it ! but i lost the paper work on what wire is for max speed. red is the low min, for furnace. it has black blue white and red wires and it is a multi speed blower. SO wich WIRE WOULD BE THE HIGH SPEED ONE
THERE SHOULD BE A SCHAMATIC ON THE SIDE OF THE FAN MOTOR WITH THIS INFO ... Air Conditioners
OK I am a dumb A--. I did not turn the power off to my Payne PG9MAA Condensing Gas Furnace. Also A/C. In my futile attempt at relocating the thermostat. I 1. did not turn off the unit 2. I did not have enough wire so I spliced in a new longer one. 3. Voila' there is absolutely nothing on the thermostat showing power. I used the voltage regulator and put the contacts one on red and the other I went in sequence to all the other wires and it read 11.00 or so volts.. If I changed the (lead) or
Depends if its a 12 volt or 24 volt system and if your meter is reading right also check meter then check red wire if its a 12 volt thats what you should have and 24 so on or you have a dead short good luck with that one just be calm a go thru all t ... Air Conditioners
I have a Rheem criterion ii gas furnace. i put bin new blower motor and i need to put connect wires to the intergrated control module blue, orange, black, red
\015\012Blower hookup on the circuit board isYellow/Orange - HeatRed - FanBlue - M2Black - Cool\015\012\015\012\015\012\015\012Let me know how this works out for you.\015\012 ... Air Conditioners
My plan jane evcon thermostat is not wired right. The furnace works fine. The air conditioner will only come on when you push the lever up hotter than it is in the room instead of cool. It will then run, but runs and runs and will not shut off. There are 4 wires, red that is hooked to screw with B by it because the blue wire has a piece of paper on it with a Y and is hooked to the Y screw, white that is hooked to one with W and green wire is hooked to the screw with G. little short red wir
Hi,\015\012Okay....two things to check on...\015\012make sure that the terminals and the wires are matched in the t-stat and the furnace board...R-R Y-Y G-G W-W ....if everything matches up then you have a fried t-stat... What you are say ... Air Conditioners
I am installing a Mars 1/3 hp fan motor. It has a black wire,red wire, blue wire, yellow wire and (2) brown wire that go to a capacitor. May Furnace has Black power wire, red wire (speed) and white common. What wire is the common to the fan motor?? I hooked it up with black to black, red to red, and white to the blue. It ran fine for 5 min then it thid my breaker in bresker box???? If the blue was not common how could the motor run at all??
Hello, Typically your common wire will be white, high speed- black, medium speed- yellow, medium low-blue, red- low. The motor could still run for a short time if it was wired wrong but will either trip a breaker or go off on it;s overload when it's ... Air Conditioners
Installed a new Filtrete thermostat on a new Carrier high-efficiency furnace. I followed instructions exactly. It doesn't work. What did I do wrong? Furnace was installed in December. Broom handle cracked faceplate of Carrier thermostat and rendered it inoperable. Installed new thermostat according to instructions. Connected white wire (labeled V+ on the old Carrier thermostat) to the W terminal on the new Filtrete thermostat. Connected red wire (labeled Vg on the old Carrier thermostat) to the
Thanks for the update, regarding the thermostat.Hope replacing the thermostat resolves the problem.Keep updated.Thanks.Helpmech. ... Air Conditioners
I have a Carrier 8000 weathermaker. Recently the blower motor began to run progressively slower and finally just bogged down. I replaced the motor, but the replacement motor has three speeds (red, blue and black wires) whereas the old motor had four (red, blue, black and yellow). Initially I hooked the new motor wires up to the circuit board the same way the old ones were, leaving an open spot where the old yellow wire was. New motor works, but at lower speeds, pushing less cool air. We liv
Found system was slowly loosing coolant through a variety of miniscule leaks in rusting part of condenser. Apparently coolant level had dropped sufficiently in the blower repair interval to where the system no longer functioned with adequate efficie ... Carrier Air Conditioners
Suburban sf30 rv unit.. I had a new board and limit switch installed. The service tech said it was working. I marked the wires when I removed the unit. I re installed the unit conecting the wires the same as when I removed the unit. I have 2 blue wires, 1yellow and 1 red coming from the furnace. There are 3 thermostat wires 1 grn, 1 wht and 1 red---The power source are 2 solid white wires and 2 blk and wht striped wires, there is power to the unit. I am at a loss as to why it will not work. T
... Dometic Rooftop RV Air Conditioner
I just got a new honeywell thermostat and it when i first hooked it up it wouldnt turn on so i check to find out which connections on the thermostat when open i changed my wire to make it correct now when it turns on it doesnt turn off. i only have 2 wire that were on the old thermostat and the new one shows spots for 3 wire do i need to run a 3rd wire to get the furnace to shut off after it reaches desired temp? right now i have to disconnect the thermostatto shut it off.?
Hello my name is Heath it will be my pleasure to assit you. If you did not turn the power off to the furnace before rerplacing the thermostat then you may have burned out the board in the furnace. But first if there is a RH/Rc terminal in the new the ... Honeywell Air Conditioners
I just installed an intertherm MB/MM 90,000 btu forced air furnace with an a/c package. I am having trouble with the low voltage wiring. Specifically, where do I put the yellow wire fromn the t-stat and where do I put the two wires from the a/c condensor. The fau has 4 wires; red, black green and gray
Well if you only have 2 wires, this could be a problem, you need 4 wire, red white, green and yellow, if you don't have these than we have to run a wire ... Intertherm P3RA-048K Air Conditioner
I have a Trane XE 1000 and attempted to replace the thermostat. When I saw that the wiring configuration was set up for a different configuration I put the new thermostat back in the box without trying to wire it. I put the old thermostat back on, wired it just like it was (I took a pic of the config before I removed it) and now I can not get the system to power back on. Is it possible I blew a fuse or tripped a breaker in the process of reinstalling the old thermostat? There was one point where
You could test this by totally by passing the stat and connecting through a wire linc.\015\012However you seem a little to inexperienced to be doing this and in my opinion you should for safety sake wait until monday,for a tech. ... Air Conditioners
Have atwood 7916II furnace and wish to wire in new thermostat. Existing wires on furnace are, white - black - red. Which wire goes to power and which go to thermostat. Thank You, Walter
... Coleman Mach III Air Conditioner
I have a York Diamond 90 Unit and my A/C quit blowing cold the other day. No Blower running, No Condensor or Compressor running. I replaced the capacitor for the blower motor and it started but no condensor. I checked the capacitor for the condensor visually and it was bulged out. I bought a new one (not the exact brand but I had a AC parts house match it up with the old one.) The new one has labels on the legs the old one did not. I have 3 wire leads off the condensor 2- Brn and 1-Red (New Capa
It sounds like you may have install it backwards. break the power and try again, if the compressor is trying to start thats a good sign. at least its not dead. Try re-installing the capicator and that might fix it, it wont hurt anything to try. ... Air Conditioners
The Coleman Mach thermostat in my 5th wheel blows its 2 A fuse a couple of times today and am trying to figure out what is causing this. Please help. I am unable to get the furnace to run even with a good fuse in the thermoatat. When I bypass the thermostat to run the Atwood furnace (red tied to white wire). THe furnace blower comes on and the burner sounds it lights for 5 seconds and then goes out. 15-20 seconds later it reignites and goes out and continues to cycle -- the blower motor
Hi\015\012\015\012Its blowing fuses because of short circuit inside the coleman mach or due to two wires being shorted with each other. You'll need to open up your thermostat system to look for the short circuit and also shorted wires.Ple ... Air Conditioners
I have a Trane Heater/AC unit no heat pump with a thermostat model 802AS32DAA that has seven wires. I am going to a five wire heating/cooling thermostat. What do i do with the two extra wires? old thermostat red wire-RC slot (24 V from A/C) white wire-W1 (???) yellow wire-Y (A/C Compressor) green wire-G (A/C Fan) black wire-B (?????) Blue wire-Y2 (????) orange wire-W2 (24 V to Furnace new thermostat therminals G Rc Rh Y/O W/B Y1 Can you tell me what wires to connect to each
From Honeywell : "If your old thermostat had Six or more wires, the replacement you have is Wrong!" ... Air Conditioners
I have a Bryant 561C central air, 5 years old, The Motor on the outside unit of this air conditioner went out, trying to sve some money on a service call I ordered the new motor and put it in my self and was able to make it run but no cool air inside the house. The motor that I took out was made by General Electric with three wires coming out of it, now the new motor I bought was made by Emerson with 4 wires coming out of it, also the lady from the Bryant dealer where I bought the motor also sen
Hi there, \015\012\015\012here is the wiring diagram of you air con unit...\015\012\015\012http://w ... Air Conditioners
EMERSON FAN MOTOR WHICH HAS A BLK WIRE PURPLE WIRE AND A BROWN WIRE WENT DEAD. SO I BOUGHT A NEW FAN EMERSON CAME WITH 4 WIRES BLK ,WHITH, BR AND BRW AND BRW WITH WHITE STRIPE. I WIRED IT BLK TO THE CONTACTOR WHITE TO THE COMM THE YELLOW FROM COMPRESSOR TO THE HERM BRW TO THE FAN BRW WITH WHITE STRIPE TO THE COMM THERE IS A RED WIRE GOING FROM THE COM TO THE CONTACTOR WHEN I TURN THE AC UNIT THE COMPRESSOR COMES ON PUT FAN DOES NOT ?????
The two brown wires go to the fans capacitor. The capacitor should always be changed with the fan motor.\015\012\015\012It sounds like your unit has a dual capacitor. One side for the fan and the other for the compressor. All you will be ... Dometic Rooftop RV Air Conditioner
My ac unit is making a humming sound I purchase a capactor an I replace the capactor I have a black black wires that is lose that and I need to know where it needs to go,On the base of the new capactor my connections on the green I have brown wire, on black wire I have 2 reds, 1 grey 1 orange, I have blue I put the black wire on the white base could you send me the right information.the number on the capactor P/N 610 - 803 - 51
When you took the old capacitor off did it have the same type of connections as the new one? If so you should have written then down, or remembered the color coding. If it's different then something is wrong. You will probably have to contact the ... Friedrich CP12C10 Wall/Window Air Conditioner
I have a LUX TX9000LC control, connected to a Carrier Model 394GA036100. The controls don't seem to control the furnace or air conditioning. The fan on the furnace runs continuously even when the switch on the control is in the off position. The only way I can turn the fan off on the furnace is to switch off the power to it. I put new batteries in the TX9000LC. No change. Thank you, Ron Casto
Ron, \015\012It sounds as though a "safety device" opened on your gas furnace......which shut off your furnace and has the fan running non-stop. Go to your gas furnace and look for manual reset switches......these switches typically have a smal ... Air Conditioners
I have a 4 wire American Standard thermastat and am trying to change it to a 3M-22. My wires are a red (R), a green (G1), a white (W1) and a blue (W2).I have no clue where to put them on the new thermastat and not sure if I have a "c wire" at all. Can anyone help...PLEASE!!!
... Air Conditioners
Need som help with a wiring question on a CD#52 AO Smith 1/2 hp blower motor. the furnace runs wiring for a white, red and black not sure which wires go where.
Look at the schematic on the inside panel of the cover you removed. It should have the schematic with the wires and colors labeled as to what goes where. The wires are a common, run and start wire. They schematic should identify the wire by color a ... Air Conditioners
Compressor I have a new compressor and a new 40/5MFD 440V ROUND Capacitor on my unit, which was put in by an A/C shop. But it has to have the kickstart to run the compressor. They say the compressor was new. The wiring diogram calls for that capacitor. Why would it need the kickstart, because thats the only way the compressor will kick on.
The jump start is installed when the capacitor is weak but not dead. It is a temporary (can last for years), inexpensive solution. The correct solution is to replace the capacitor. ... Goodman Air Conditioners
Got a honeywell t8400c thermostat i'm trying to replace with a honeywell rth3100 honeywell thermostat but only have yellow green red and white wire on the old and don't know where to put the wires on the new
R--- rc or rh y--yellow g---green w--white red is power yellow is cool g--fan white is heat ... Honeywell Air Conditioners