Having problems with your Air Conditioners ?
Outside unit not working
You most likely need a service guy to go out and take a look
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
I am working on a M # GPG13420901AB. This is a 3.5 ton package unit that replaced a 3 ton package unit on 1700sq/ft single level home. Old unit was working fine but was replaced when the home was renovated. The new unit will not hold temperature in the home when outside ambient climbs above 83-85 degrees. Refrigerant pressures early in the day (70-80 degrees ambient) look fine 70 suction 200 high 9-11 degrees SH. Late in the day with outside ambients around 90-95 degrees, inside temps 75-78
It sounds like you are low on charge. I think you have a thermostatic expansion valve and you need to check the subcooling, you should have 12 to 15 degrees at 95. At 95 degrees your head should be about 280# for a 12 or 13 SEER unit or higher depend ... Goodman Air Conditioners
I built a house in Sept. 2007. I purchased 2 rheem air/heat units. I have had a lot of problems with one of the units. Unit Rheem rpne 036jaz. I have had four different repair men out to fix the unit and still have the same problem. I have had the circuit boad replace in the outside unit three times and replaced the thermostat and the contactor on the outside unit. The inside fan will kick on but the outside unit will not. I can reset the unit inside and it will work for a little while but then
... Air Conditioners
My fan and heater work fine, but today I turned on my air conditioner for the first time this year. It did not feel like it was getting cooler so I went outside and noticed that my outside unit was not working. I went and checked the breaker and noticed it was tripped, so I turned it off and turned it back on (the breaker). Then all orf the power went off to my house. I then reset my whole breaker box and I heard what sounded like my outside unit explode. I ren over to it and it sounded lik
You had a refrigerant release. Probably two lines rubbing together in the outside unit. I have repaired several of these with this problem. It involves repairing the lines by silver solderingthen pulling a vacuum/ purging with nitrogen an ... Carrier 36KCARMS Air Conditioner
I replaced my outside unit with a 3 ton goodman heat pump unit. My old unit was a 3 ton bryant and the compressor burned up in it. I left the old unit under the house since it seemed to be in good condition. the pump worked fine on ac to start off. But then you had to switch it in heat and back to ac for it to work. So the tech replaced the expansion value and put filters in both lines. I still have to switch it back to heat to get the ac to work. The tech told me that i would have to repla
You said it had rwo filers on the line. I know one is a liquid line drier. If you have one on the suction line it need to come out ASAP. The trash in the line can be removed by running in cool.pump down unit replace drier. While the unit is pumped ... Air Conditioners
Outside unit will not turn on. Inside fan works fine. This intertherm unit is an upright, 6yrs old. Model number unkown. Fan will turn. No hum coming from unit. inside condenser sits on furnace model # E2EB-015Hb. Freon charging is outside on the lines coming from outside unit.
Hi! You may want to start on having the power supply checked. Good cause why the unit won't power up. Have the compressor checked too just to be sure. ... Intertherm Air Conditioners
Had a ac tech service central heating unit for the fall. Tech left and I left to do some errands . Now AC unit is not cooling its blowing warm air. I turned the circuit brks off and on inside and outside. I have also checked to see if unit was left on heater. thats not the problem. If I turn theAC on the fan does not turn on outside and there is no sound coming from the unit outside HELP!!! AC was working properly before this.
It may not help but it sounds like the tech took a control wire for the cooling circuit loose at the indoor air handler/furnace so that he could bring the heat on to check it, and forgot to hook it back up. That may not be the case, but if it is it w ... Air Conditioners
Outside condensing unit smells burnt with no part working outside, inside unit fan blows . will bad fan keep everything from working? goodman ck49-1b
Shutdown the unit and check the condensing fan motor as well as the compressor. ... Air Conditioners
Outside AC unit working, but inside there is no air flow and fan inside will not work unless it is turned manually. Also, a little ice on outside unit.
Depending on what type of Thermostat you have, it is usually as simple as setting a jumper for Electric heat instead of gas.\015\012If you have a digital Thermostat then turn off the power to the Air handler and remove ... Carrier Air Conditioners
The cooling unit outside is not working. Its a Midea split system and the indoor fan unit works for a bit until all the lights flash together and it stops responding. The external unit (that does the cooling) is not working
Your compressor may have seized up or burned up or blew a fuse. you may want to call an ac tech cause you cant really do much yourself with it. if the compressor is seized you may be able to unstick it by taking the back off the ac unit and hitting t ... Midea MWB-05CM1 Air Conditioner
I have a Lennox Merit series residential AC unit, my furnace engages and blows air but the outside component WILL NOT turn engage! Furnance fans runs continuously with cycle as if outside unit was working but the outside unit will not engage.
... Air Conditioners
I have a ducted sanyo split system. The model number is SPW-C361GH5TU. The unit in the ceiling stopped working about 4 weeks ago. The outside compressor would start up but stop after a short period of time. I managed to get a technician to work on the unit. He said it was the PC board. It took two weeks to get the part but when it was fitted, the unit still didn't work and the technician told me the problem was with the fan motor. Another two weeks have elapsed, and he now tells me it will take
You can order the part from link below.:--\015\012they provide quick deliveries:--\015\012http://www.jpcparts.com/103-546-8441.html\015\012\015\012you can p ... Sanyo Split System Air Conditioner
Hi Expert, my reverse cycle aircon is Samsung model name=AQY09NSBN, only fan is working on the outside and inside unit at the moment, no heat air or cool air coming out of the inside unit, even tried with different temperature setting. Everything was fine till my gutter downspout was blocked and the switchbox outside near the unit was flooded and the aircon was on and off by itself every three seconds, so I turned the aircon off from the main switch outside. I got an electrician to replace the
Hi, and no your warranty is not void due to a flooded disconnect box, this is a lie!! If both fans are running, and you have no heat or cooling, the compressor is not running. This is a heat-pump with a reversing valve. The indoor unit has a control ... Air Conditioners
Have AMCORAIRE mini-split purchased in 11/08 and installed in new guest cottage on 7/17/09 by local AC tech. in Cocoa, FL. Unit worked fine for approx. 7 months then stopped working with error code F!. Called AC Tech who installed unit and he called Pridiom tech support and spoke to Alan while trouble shooting unit. They determined that trouble was in circuit boards and suggested replacing boards, which were back ordered or buy new outside unit. The unit is a 12,000btu mini- split with heat
Try this link. They will be able to help you with your concerns.\015\012\015\012\015\012The FixYa Team ... AmcorAire UCHW-H12AF2 Split System Air Conditioner
My unit is running but not blowing cool air. I went outside and the condenor fan was not moving. Took a stick and shoved a blade and the fan started moving but the air is still not cool inside. I did notice the air coming through the unit outside after fan was blowing was cooler than my 2nd a/c unit that was working fine. I wondered if the entire unit was frozen. I turned off unit at thermostat and figured I would see what happens tomorrow
Sometimes on new units it is common for the fan to not start until you give it a push. Did you happen to hear if the compressor was operating? If the unit was froze-up the Insulated Suction line would also be iced over as well. If it wasn`t it is mor ... Carrier 38CKC024 Air Conditioner
I am working on a GE air conditioner Model # AZ35H15D5BMI, Serial # TA659138, manufactured date 10/01, I replace the control board part number WP26X10018 and the board fried a resistor or a diod. I have purchased a new control board and don't want to burn this board. I need a schematic of the unit to make sure I rewire the unit properly. There is no schematic in the unit that I can find, I have slide the unit out and looked in the outside unit for paper work or a diagram but have had no luck
Dear friend i got some model number for you... have a look....please click here and have a look... ... GE Air Conditioners
I have a Carrier infinity model 38tdb037-3. The outside unit will not come on. the control board on the outside unit shows an amber led on status 2.it is a steady constant flash.the error is an apparent stand by/on demand.munualy depressing the contactor forces the unit to run and seem to work fine. communication is good. the inside unit shows two green leds and one amber constant flash. any ideals. maybe bad control board?
... Carrier Air Conditioners
Sometimes, when the inside blower shuts down, the outside compressor and fan motor continue to run for some time. Other times, when the inside fan motor is running, the outside fan and compressor motors are not ... if I press the outside reset button, it starts up When both inside fan motor and outside fan and compressor motors are running, it works fine ... warm air blows out of registers. Other than that problem, both units work great!
Sounds like you have a dirty condenser. You are going to need to disconnect the power at the outside unit on the wall by pulling the fuse block out. Take a good look at the louvered covers that are attached to the outside of the unit. Remove the scr ... Ruud UAKA060 Air Conditioner
Goldman mini split model msg12hwn1n. I set the unit to cooling the louvers open, outside unit works for a minute then the louvers closed and outside unit stop, inside unit start flashing green continually in operations
... Air Conditioners
My colmen central air unit is not working properly. The Outside unit is not working. The problem initally arouse in June, but it "self corrected" after having the A/C unit turned off. Since that time the unit has run perfectly untill now. I did look for a reset button, but was unable to find one. The system (at most) is only 4 years old.
If nothing is running outside at times you probably have a weak contactor coil that is not pulling the contactor in all the time. If the outside fan comes on but not the compressor, the compressor is over heating and ... Coleman Air Conditioners
I have a question about matching up BTUs for the inside and outside units as I have had conflicting info from 2 different repair men. We have a 36 BTU condenser outside (Mitsubishi Mr. Slim) and a 24 BTU unit in the main living area with two 9 BTU units in each of the 2 BR for a total of 42 BTU on the inside. The installer of course says this is perfectly fine, another repair company said this was the reason why we were having so many problems with the unit. When it works, it's great. However i
Hello,In a traditional air conditioner setup where the compressor runs at one speed, the condenser and evaporator need to have matching BTU ratings. If the condenser (compressor) is too small, it will not be able to cool effectibely, and ... Mitsubishi Mr. Slim MXZ30TN Air Conditioner
I have central air ( Dimond 80 York Heating Air conditoning Unit ) My air conditoning unit has stopped working. The board has checked out ok.but there seems to be a voltage problem some where from inside to the the air conditoning unit outside, the voltage reading is 26 inside and only 10 outside not enough to start the unit . Do You have any idea as what the problem might be? Thank you, drewskie
Try the following step.....On a call for heat, the 24 volt thermostat sends a signal to the\015\012control module. The control module will indicate a call for heat with a\015\012light on the control either blinking or remain solid d ... Air Conditioners
Ruud UPNE- 036JBZ 2 years old (outside unit) Ruud Acheiver air handler 1 year old inside unit... outside unit will not come on. voltage (120) ready at contacts. push manually and it comes on. yellow wire and brown wire go to board. no power on these when inside unit is running. power bill has doubled......must be running off heater coils? What would be the next thing to check. I did look at thermostat seems to be working normal. Can't get knowledgeable help.
... Air Conditioners
Heating problem hello! My air conditioner stopped to heat. (there is a around 8 degrees C, outside and 16 degrees inside). It worked just fine, and now, when I switched to heating mode, there was nothing. the defrost LED ond the inside unit is switched on, but air is not comming from the unit. Cooling mode works fine. If you could please help me finding the solution for my problem. Thanks in advance. RAdan GE AIR CONDITIONER SPLIT SYSTEM WON'T WORK ON HEAT CYCLE Seems to work ok doing eve
Hi Radan, Did you get this problem solved? We have an Electrolux Kelvinator Split System and ours is doing exactly the same thing. I am struggling to find a solulution. Would be great if you can offer any advice.\015\012\015\012Thanks Nic ... Air Conditioners
Hi, just replaced the capacitor thinking that would solve the problem but it appears it did not. The motor outside would kick on the unit inside would kick on but the blower motor inside works sometimes and wont other times. Basically, the unit will work just fine all day then we notice the house is getting warm, check the inside unit and everything is running fine but the blower motor is not circulating the air. I have a goodman a30-10 unit. I read where some people said the relay could be bad
Turn off the power to the air handler(indoor unit). Remove the access panel. From the motor,trace the wires back to the fan relay. One wire will probably trace back to the incoming power terminal. The other is the fan relay. It could be intermittent ... Air Conditioners
Heat pump gets ice covered when heat is on. Cooling works fine. There is two brown wires coming from the unite in the attic to the outside unite. One of the wires has come loose from the outside unit. I don't know where it goes or if this is what is causing the freezing. Thank you, Ky Girl
Hello,KY the defrost function is not working.The wire goes to frost sensor or the outside unit control.It is LOW voltage wire.Turn the unit off and carefully look for a abandond/bare wire.Maybe a single wire with a wire nut/cap or splice.Reconnect th ... Air Conditioners